Response from Trenchless Innovations Inc.:
Thanks for your review, Ronald! We are happy to hear you had a great experience with us. Thank you for choosing us for your air duct lining - you're on your way to cleaner, healthier air! Happy Holidays to you!
Encapsulated all deteriorated underground duct work with our duct lining material. The air in the home is now environmentally safe to breathe.
Our customer was getting a musty smell coming from the underground air ducts so we applied our duct lining product to all the underground duct work under the slab home to seal the underground system and line the existing duct work.
Applied trenchless cast to all deteriorated underground duct work to give pipe a strong structure.
Encapsulated all deteriorated underground duct work with our rubberized duct lining material.
Applied Trenchless cast to all deteriorated underground duct work to give it a strong structure. Encapsulated all underground duct work with our rubberized duct lining material.
Televised sewer line from inside clean out stack. A section of the pipe is collapsed, causing water to leak out of pipe and under the customers home.
Just completed cleaning and sewer lining 30 feet of 4 inch cast pipe under basement floor.
Video inspection of underground air ducts. Ducts are cardboard with metal connections. Cardboard showing signs of mold and deterioration due to water issues. Outside gutters are clogged and downspouts are dropping next to house. Homeowner needs to extend downspouts and clean gutters. Once water issue is resolved the ducts should be Trenchless Casted with mortar and then spray lined with Duct Armor.
Televised underground duct work with cardboard ducts under slab, water enters duct work with heavy rains causing the cardboard to deteriorate and in some cases collapse the weak pipe allowing dirt/ backfill to enter the duct work.
Televised underground duct work for a customer, the entire system underground had water in the ducts recommended a few options to eliminate water from getting into duct work before we can restore the damaged ducts.