Televised Sewer from catch basin on side of house but could not get all the way to the main due to a blockage. Located and it is in the parkway. Suggest ridding to clear blockage then retelevising to main. There is a location in front of the house that is heavily cracked where a connection is possibly drain tile or downspout. Suggest digging to make repair then installing a clean out at that location.
Televised sewer from outside clean out. Sewer was backed up at first when we arrived, but we were able to clear with the camera. Sewer has heavy roots going upstream to house and the cast iron is cracked on top allowing roots in. Downstream has roots at most joints for first 30ft. Provide proposal for lining