The crew who came to install our sump pump were very devoted, hard working, and knowledgeable. They took care of the original problem, and also included other areas that might factor in in the future besides the sump pump. They took the precautions needed today with distancing face masks when having to come into our home. We are confident our problem has been solved, thanks to them!
Response from Trenchless Innovations Inc.:
Thank you for your review, Lillie! We are delighted to hear that our team was able to quickly and safely solve your problem for you. We appreciate you choosing us for your sump pump service. Thank you for your support and please reach out to us should you need anything further. Stay safe and healthy!
Televised ducts under slab floor. Ducts are concrete with metal connections and fittings. Concrete is in good condition and metal is only showing slight signs of rust. Plenum also has very little rust. Customer had water in ducts after a heavy rain fall. All the downspouts are properly extended away from the house. Believe this wTerinsystem was an isolated event due to the condition of the ducts. Suggest spray lining the ducts with Duct Armor duct lining material in order to encapsulate the concrete possibly Transite ducts.
We are installing a perforated sump pump pit outside next to the customer’s house. We are going to core through the foundation wall and install a section of perforated pipe to relieve the water pressure coming in to the air ducts. The water will be discharged underground 10 feet away from the customer’s house.
Inspection of underground air ducts. Found water is ducts. Extending downspout above ground away from home
Televised townhouse and found rusting duct work and dirt. Cleaned ducts and rebuilt plenum and registers. Sprayed system with Duct Armor to seal and renew ducts.
Video inspection of underground air ducts. Ducts are concrete with the box under the furnace completely deteriorated. Ducts should be spray lined with Duct Armor.