Came out for prepaid tuneup. Ac is a 2019. I replace filter today it was provided. Temp split is in required range. All electrical components are testing properly and working properly. LRA is high on the compressor amps. It’s right next to where it supposed to be recommend adding a hard start kit to lower this and prolong the life of the AC. I hosed down condenser coil‘s. Refrigerant levels are testing properly. Capacitor on the blower housing is testing at a 5% drop should not exceed 6%. Coil and blower both clean. See health report card for questions. Ac was when I left the call. Option for hard start kit was declined today.