Would hire again
Tech did a great job - very thorough and professional. Would highly recommend.
Super pleased. He did a great job and explained exactly what he was doing and recommended doing
Nick did an incredible job installing a SimpliSafe doorbell & GFCI outlet. Couldn’t have asked for better service. Highly recommend this company to all!
Nick, was quick, informative and friendly. Also, very polite to kids.
Alex worked hard and fast to fix the multiple electrical problems in my currently 110 degree attic.
Thorough and complete work from nick everytime he's worked on our house. I've been happy with their work everytime
This estimate includes the installation of a new microwave receptacle. We have installed new microwave receptacle. Existing wire is a dedicated circuit.
Replaced 14AWG wire going to receptacle under panel with 12AWG wire. Replaced standard 15Amp breaker with Arc-Fault and GFCI Dual Function 20amp breaker. Replaced old receptacle with Tamper-Resistant receptacle.
This estimate includes the repair of the existing circuit involving the living room receptacles and the kitchen lighting We have repaired the living room circuit. We found switch at front door wired incorrectly.
This estimate includes the installation of a customer supplied ceiling fixture and ceiling fan on the 3rd floor
I removed and replaced old motor in attic fan. The previous electrical installer had it set up unsafe and incorrectly so I re supported the fan motor and installed a automatic kill switch next to the fan. I tested the fan and it worked great. Set it to 105 degrees Originally we were going to add a arc fault breaker for that circuit but the age of the devices we held off and I informed customer they should have us out to re device either that circuit or the whole house due to the age of the devices and the fact they are stabbed in the back Also there was a 6 inch vent going to the existing attic fan blowing out from the bathroom to the motor of the fan. I removed that and customer will have to have someone to vent that through the roof because it is unsafe for that moisture to go directly to a attic fan motor I installed a QO flush mount whole home surge protector. Customer has a 18 month warranty on work preformed
Ei2c-This estimate includes several repairs to the living room and master bathroom circuit. We have repaired the circuit, poor terminations were found in receptacle outside of bathroom. In addition we have installed a proper electrical box to house wires associated with back door light. Lastly we have gone through this circuits entirety and can assure no further wiring concerns at this time.
Removed older original cook top and installed new customer supplied one in its place. Unit was the same size. I repaired wiring in junction box under cooktop and connected new wire from cooktop properly. I tested unit out once installed and it was working properly.
We have installed a new customer supplied ceiling fan in the daughters bedroom.
Installed a new outlet by the back sliding door for pool equipment. Itâ€™s a weather resistant tamper resistant GFCI with a in use bubble cover. I siliconed around the box to protect from water damage Itâ€™s on a 20 amp circuit
I removed a over fused 50 amp breaker and installed a 40 amp breaker in its place. Also removed a over sized 40 amp breaker and installed a new 2 pole 30 amp breaker I also removed all double tapped neutrals and separated them under different screws on the ground bar Due to the age of the panel and style I would recommend a new electrical panel in the near future but as for now this panel is fused properly Also put nolox on wires attaching to breakers to avoid over heating
Removed receptacles in bathrooms and made them all GFCI through the line side Replaced outlets outside with weather resistant GFCIs and installed in use bubble covers and siliconed around the box Removed switches in up stairs bathroom respliced the boxes and hooked and clamped new switches Installed new light fixture in bathroom Replaced switches for stairway and installed new light fixture in uspstairs hallway Replaced gfci under the electrical panel in utility room
Removed fan from top floor hall bath and installed a new customer provided fan/light combo.verified proper operation of completed work with customer. Provided estimate to run a circuit for a cooktop.
Repaired wiring to bathroom GFCI outlets. Installed new 4-way switch in place of existing switch at the top of the stairs for the 2nd floor hallway lights. Corrected 3-way setup up for garage lights by adding a 3 wire to the back to back switches. Replaced outlet on dinning room wall closet to the kitchen. Disconnected motion sensor to back walkout light next to the kitchen. Quote to remove existing federal pacific panel and install new 200 amp main breaker panel in its place. We will pull electrical permit and coordinate scheduling with power company. We will also add an outlet out of the new panel on the exterior of the house as well as replace customer supplied ceiling fans in upstairs rooms. we will also correct 3-way switch setup in the basement to work as customer requests.
Removed and replaced a 90 amp 2 pole qo breaker for sub panel
Installed new customer supplied video doorbell on front of home and ran new low voltage line from new doorbell to a plug in transformer we installed in the outlet behind it on the inside of the home. We removed washer outlet and installed new GFCI in its place.