Larry was exceptional. Called and arrived on time. Very courteous and answered all questions. I will hiring Hass & Sons again - 5 out of 5 Stars
Alex was very knowledgeable in explaining different issues that I asked about, issues that may arise and options.
Alex did a great job of rewiring our dishwasher to our house’s electrical system. In just two hours he was able to diagnose the issue, provide a decent quote, install a new outlet under the sink, and get my dishwasher up and running again with no issues at all. I will definitely be reusing this company again in the future.
Really appreciate the service provided. We were able to accomplish many solutions in one day.
We had such a hard time finding an electrician. When we contacted Haas , from the very beginning we were treated well and Mike the Electrician did a great job.
The service man was right on time. He was very knowledgeable and efficient. The price seemed a little high but as the service provider explained, if we had more jobs to be done we would have received a considerable cut in cost. Next time we will try to take advantage of this price cut. I would definitely recommend Haas and Sons.
Alex was knowledgeable, courteous and thoroughly explained each step of the process. I'm pleased with work down in my living area.😊
I re deviced the dinning room and the kitchen circuits I spliced all appropriate wires together and pig tailed off them creating a far better connection that was there previously. I then stripped the wire and hooked it around the device screws then clamped it down and tightened down the screw. I installed new gfcis and tamper resistant receptacles with new plates. Many of the existing receptacles had burnt wires and damaged wires I also removed and replaced two stacker switches in the upstairs bedrooms Also removed and replaced two single poles switches in the hallway bathroom We will need to return to install a 2 pole arc fault 20 amp home line breaker Customer has a 18 month warranty Installed a 2 pole 20 amp arc fault breaker for kitchen and dinning room circuits 10-21-21
Customer had lights out due to a broken 4 way switch. I also discovered the three ways and 4 way were wired incorrectly. I re wired the boxes to make all the switches in the laundry room work correctly then I replaced the switches due to the 4 way being broken and the 3 way when you first walk into the room to the left having a crack in the switch I also replaced two bulbs outside for a security light to stop the light from flickering. Itâ€™s possible itâ€™s the fixture. If it is and the customer has us out to replace the fixture we will use the 95 dollars for the bulbs toward that price since the bulbs are new and we supplied them
Customer had 2 outlets in bedroom not working. Problem was in the back plug on the porch. Replaced tha receptacle with a weather resistant gfci and extra duty in use bubble cover. Also replaced the front receptacle. Verified proper operation of all completed work.
I removed and replaced all receptacles on the home gfci circuit That included the outside outlets, the master bathroom the upstairs hallway bathroom and the receptacles in the garage on the walls I replaced the receptacles with GFCIs and I replaced the outside outlets with weather resistant GFCIs with in use bubble covers I line sided all the wires after splicing them and pig tailing off the splice. I also re fed the gfci on the right side of the garage due to a broken wire in the wall. I cut a old work box where the wire was broke and ran a jumper between the boxes. This was able to power up the outlets outside and the other garage outlets I had to remove and replace a weather proof box out back by basement door for the gfci because the existing one was damaged Customer has a 1 year warranty on this work I also removed and replaced a gfci in the garage that is controlled by a light switch by the front door. This operates a lamp post out front 30 day warranty I also looked a
Customer called us out because of basement lights flickering. Ballast were failing in all 6 light fixtures. In order to fix said problem we removed all ballast and re-wired lights to 120volt LEDs. Installed all new LED bulbs(24).
This estimate includes the removal and replacement of 2 bedroom ceiling fans. Customer to supply fans. This estimate includes the removal and replacement of 2 50cfm bath fan motors on the second floor. This estimate includes the installation of a proper light box to support the existing vanity in the master bath room. We have determined that the stove whip was never secured properly. This resulted in arcing, electrocution hazard, and damage to the wall from excessive heat. We recommend replacing the damaged unit. Lastly we shall return on the 19th to complete scheduled work. We have collected the 30% down. We have completed all scheduled work.
Replace a breaker that was tripping for kitchen lights and outside front plug. There is a heater for a water line that was left plugged in and has multiple spots between extension cords that can let moisture in. Breaker that was replaced is in the number 8 spot.
The light on the side of the home has a bad sensor and a missing knockout seal. I removed the bulbs and installed a knock out seal so no water can get into the weather proof box. The fixture will need to be replaced if the new owner wants it to work
We re-wired the disposal on the last visit, which fixed the power loss to the GFCI next to the sink and the outlet to the right of it. On this visit we found that there was another live circuit in the junction box hidden behind the wall above the disposal switch. We cut the wires off in the attic and set a new visible junction box and dropped a new wire down to the dishwasher and re-fed the outlet on the far right of the counter. All the outlets on the right side of the sink are now repaired properly and working perfectly.
-Remove and replace dining light with customer provided chandelier -install customer provided fan on porch -install customer provided fan in bedroom -remove and replace stair chandelier with customer provided light fixture -add a new receptacle behind tv stand in living room -add new receptacle in garage from receptacle in room with shared wall Verified proper operation of all completed work with customer.
I removed all devices on the home gfci circuit and replaced them with GFCIs and line sided all the wires so if a gfci trips it only trips that device and doesnâ€™t affect the other devices on that circuit which include the bathroom receptacles the outside receptacles and the receptacle by the panel for the internet. I replaced the outside receptacles with weather resistant GFCIs with in use bubble covers and siliconed around the cover 1 year war I also removed and replaced a switch and receptacle in the vanity room And removed and replaced two lights in upstairs bathroom 30 day warranty
This estimate includes the alleviation of all double tapped neutrals in main service panel. We have alleviated all double tapped neutral wires in the main service panel.
Replaced burnt up devices on front of the with new weatherproof devices. We put silicone around the covers to help keep moisture out of the boxes. Provided quote for panel upgrade/ heavy-up
This estimate includes the installation of a new 120V receptacle in the basement to be located at rear entrance, fed from closest source. In addition we have shall be required to install GFCI protection. We have installed a new receptacle in basement. Fed from outside receptacle.
Installed a new Haas and sons supplied dimmer to control the recessed lights in front of the basement stairs and install customer supplied dimmer to control recessed lights in living area. Both dimmers are in the same switch box.