Repaired wiring to bathroom GFCI outlets. Installed new 4-way switch in place of existing switch at the top of the stairs for the 2nd floor hallway lights. Corrected 3-way setup up for garage lights by adding a 3 wire to the back to back switches. Replaced outlet on dinning room wall closet to the kitchen. Disconnected motion sensor to back walkout light next to the kitchen. Quote to remove existing federal pacific panel and install new 200 amp main breaker panel in its place. We will pull electrical permit and coordinate scheduling with power company. We will also add an outlet out of the new panel on the exterior of the house as well as replace customer supplied ceiling fans in upstairs rooms. we will also correct 3-way switch setup in the basement to work as customer requests.