This solution includes the installation of a new light in the first floor powder room in the ceiling. Also it includes new wall sconce lighting on second floor landing area, replace chandelier in bedroom #3, stairwell light removal with new recess light to replace, relocation of receptacle at dining room nook existing at countertop height to be lowered, installation of 3 receptacles in basement sitting area, and lastly the adjustment to the foyer chandelier. We have begun the renovations, powder room fixture and stairwell light have been installed. We shall return next Wednesday to complete the scheduled work. Today we have installed the 2 wall sconces, receptacles in basement area, finished powder room, adjusted the foyer chandelier, installed receptacle near dining area and begun the light fixture in the upstairs room. In addition we have added a 3rd sconce and an additional receptacle to be installed upon our return on the 4th of January. We have tied in the basement receptacle
This solution includes the abandonment of the Kiln circuit and have it re-worked for EV charging purposes. Gfci protection included. We have collected deposit and shall return tomorrow to complete the installation. We have completed the installation of the EV receptacle.
This solution includes a new dedicated circuit for the kitchen lighting in the basement. This solution also includes the, installation of an audible GFCI for sump pump equipment, common trip handle breakers and the installation of whole home surge protection at the main panels. Lastly we shall install the customer supplied foyer light We have installed the new home run for the troubled basement kitchen lighting, power has been restored. In addition we have installed proper common trip handle breakers for the multi feed circuits, replaced the damaged looking breaker that was indicating a tripped circuit. Lastly we have installed GFCI protection for the sump pump area and installed whole home surge protection for both panels. We shall return next Wednesday to install the chandelier in the foyer. We have installed the foyer chandelier, the living room chandelier and have condensed 2 receptacles into a single two gang box. Lastly we have condensed 2 switches into a single 2gang box.
We have determined that the home is suffering from a dropped or lost neutral wire at the meter can. We observed severe corrosion across the BGE termination on the neutral wire in the meter can. Problem was intermittent but seeming to be a constant now. We Strongly recommend that BGE repair these connections, this matter is urgent. In addition we have installed a whole home surge protector at the main panel.
Service charge for a car charger estimate
Customer had GFCI in basement unfinished area (under breaker panels) that was constantly tripping. I found that only one wire was causing the GFCI to trip. I removed wire and capped off in the box and tested all the outlets that it had fed. All outlets were working. We were unable to find what this wire went to.
Remove and replace light fixture in bedroom with customer provided light. Verified proper operation of all completed work.
Quotes to replace bath exhaust fan and install GFCI for toilet lid.