Very Professional and friendly! Very knowledgable in electrical work. But pricing is a little on the high end.
Alex was amiable, and a very serious worker. He immediately put me at ease with full confidence, even when I added other minor work. I am planning another job for him, and I know it will be done right. Most important, the women in the family are ecstatic. Fully satisfied. Yes, cost is a bit higher than I wanted, but I want to have full trust in the work and expected that going in.
Nick was thorough, professional and patient. He took time to explain the work he was doing.
This is my second time hiring this company. Michael was fantastic. He went above and beyond. He got all five of my ceiling fans installed and working correctly with the other smart devices in my home.
Installation of new whole home surge protection to prevent harmful voltage spikes while also protecting home appliances.
This solution includes the installation of a customer supplied EV charger. We have installed the customer supplied Charge Point EV charger.
This solution includes the installation of a new Arc-fault breaker for the master bedroom circuit. We have installed a new breaker to control the master bedroom.
Install new receptacle in living room behind tv within the exterior insulated wall using existing receptacle directly underneath location of tv. Install new receptacle in office closet on second floor using existing circuit from outlet in the hallway on opposite side of the wall in closet. Install new receptacle in daughters bedroom on second floor for nightlight in her closet using existing circuit and receptacle on opposite side of wall in bedroom.
Replace the receptacles in the 2 bathrooms upstairs Repair double tapped neutrals in the panel Install whole home surge protector
This estimate includes the installation of a customer supplied whole home surge protector. We have returned and installed the customer supplied surge protector.
This estimate includes the installation of a dedicated 120V 20A circuit to be terminated in a GFCI receptacle at the customer’s desired location. In addition we shall install a stack switch to replace the 2 single pole switches at garage, this shall allow space for a new GFCI receptacle. We have collected the deposit and shall return next Wednesday to complete the scheduled work. We have completed the scheduled work of the installation of the new dedicated garage circuit in the installation of a GFCI and stack switch by the doorway to the home.
I ran a dedicated circuit from the main electrical panel in the basement to a designated area customer will use for gym equipment. I ran a 20 amp circuit (12-2 romex) and stapled it throughout the unfinished basement ceiling from the panel and then installed a single gang new work box with a tamper resistant receptacle and a nylon unbreakable plate. Then in the panel i installed a 20 amp single pole square d homeline arc fault/gfci breaker combo #review
We have troubleshot the power loss at the home and concluded that at the disconnect at the meter stack does not have 240V leaving the disconnect. However leaving the meter, 240V is present. The breaker in the disconnect enclosure is bad and needs to be replaced. In addition, due to the existing and inherently dangerous installation of the existing electrical wiring feeding the home’s service panel we cannot perform a repair. Lastly the land from the meter stack to the home is not owned by the homeowner, so this task of correctly installing feeder wires to the home, C-20, might fall on the management company who owns the land.
Customer was experiencing a power loss in certain areas of the home After diagnosing the issue And bringing some other concerns to the customers attention he decided to get these things taken care of while I was here so by the side door there Were two broken single pole switches in a two gang switch box that I removed then I re-splice the box and I replaced the two single pole switches with new single pole switches When you go into the kitchen there is a two gang switch box that had a old dimmer and a single pole switch and in the box things were miswired so I rewired the box correctly then I replaced the dimmer switch and the single pole switch In the electrical panel I replaced two home line single pole breakers been installed a BR tandem 15 amp breaker panel is rated for tandem breakers and it is a BR style electrical panel online breakers fit but are not permitted to be in that style of panels I also diagnosed an issue in a switch box by the front porch and after rewiring the bo
We have installed the new dedicated 240V 50A circuit for the EV charger. Circuit terminates onto receptacle in garage area. In addition we have installed a new 120V circuit in the garage terminating onto a gfci receptacle near the EV charger. Lastly we have installed a new whole home surge protector. We shall return when the 50A GFCI breaker arrives. In the mean time we have installed a breaker for temporary use. We have returned and installed the GFCI breaker in the panel. We have verified that the vehicle charges with the GFCI breaker installed without nuisance tripping.
Install ceiling fan box in the upstairs room with attic access This quote does not include the final assembly of the fan just the wiring
WO-TNFR81833 Customer had the stab wire style devices for mobile homes through her home. Some of these switches have begun to fail. We removed the kitchen switches (3), bedroom switches (4), master bathroom switches (3)and the foyer switches (2) and installed new pvc boxes with new toggle style switches in their place. All the lights are back to working properly.