WO-TNFR77299 Ran a new 30 amp line from the basement near the furnace up to the front walk in area for a future dryer. I removed a floating air splice and set a new junction box in its place. I replaced the stack switch that was broken in the bathroom that controlled the vanity light and ceiling fan. I also removed a switch in the kitchen and tied wires through and installed a blank plate.
This Estimate includes the installation of a new 240V 30A circuit to provide power to pier boat lifts. This includes new sub panel, GFCI protection and adherence to NEC standards. We have taken deposit and shall return on the 17th of January to begin work. We have begun to trench and install conduit. We have returned and demoed all existing damaged conduit and wiring, completed conduit run, pulled new wiring, set sub panel and back filled the trench. We have completed work to the sub panel and we shall return to troubleshoot the existing pier wiring. We have determined that the pier wiring at this time is working order, we did replace receptacles at pier to clear existing faults. All work is completed. 1 year warranty on parts and labor.
Customer was having an issue with 2 seperate lights in the basement rec area. I found that the surface mounted light in the center had gone bad and the dimmer controlling the single recessed light had gone bad. I replaced the dimmer and they will order a new light when they find one.
We have installed a new 3prong 50A receptacle in the kitchen.
I removed and replaced a light switch in living room And in the hallway bathroom I remove and replaced a receptacle in a guest bedroom I re supported a 30 amp plug in the garage Customer has a 30 day warranty on all work preformed
Moved outlet over 4ft so that a door could be installed.
Installed new data line