Very good appointment with experience and extremely good service on my device/Sauna
Micheal is the best! Very nice communicate everything that needs to be fixed, and how it will get done.
Excellent, prompt, meticulous, thorough, great analytical ability, found the problem (not easy) and amazingly was able to fix it. Thank you, Nick and Chris!
Mike and Chris were so helpful figuring out everything that I needed for a swim spa install. Five stars!
We had a master bedroom ceiling fan/light combo replaced and our electrician Michael was fantastic! He was friendly, polite, knowledgeable and efficient. We will definitely use this company again.
Efficient and at a good price
I have used this company multiple times because of there efficiency and reasonable cost.
This solution includes the installation of a dedicated 240V 50A circuit to be terminated into a receptacle for EV charging. Receptacle shall be GFCI protected. We have installed the new EV circuit in the garage.
We have delivered pricing regarding the repair/replacement of the existing bathfan. Membership acquired.
This solution includes the bypassing of the photocell, wire repair at junction with photocell and the installation of a new GFCI to now protect only those exterior lights at wall near garage. We have installed a new gfci to protect the outside lighting. This shall prevent the fridge receptacle from tripping. In addition we have bypassed the photocell at wall near garage.
Reason for today’s visit was to check power loss to the living room. One investigating issue I found burnt up backstabbed devices in the living room. Home was wired in the late 80s and backstab only devices were used. This means that these devices are unable to have tight connections by screw down terminals. The entire home has these devices throughout. Backstab devices have we connections in cause the devices to overheat internally. This causes the connections to become weak and eventually break apart resulting in power loss or worse. To remedy this issue we would recommend re-device in the entire home. To remedy the power Lost in the living room the living room receptacles will need to be re-device. We replaced the three receptacles located in the living room and power was restored. We recommend not using space heaters or anything else with heating elements in them on backstab devices. Space heaters should have dedicated circuits for use. #review
Reason for today’s visit was to troubleshoot hardwired sauna in the backyard that is not working. I tested the voltage and everything is reading properly. I’m getting 245 V inside the unit and 122.5 on each leg to ground. When the unit is turn on nothing happens it does not heat up. This is a warranty issue with the sauna itself. #review
Reason for today’s visit was to repair power loss to second-floor hallway light as well as the bedroom ceiling fan light. While troubleshooting I found that the hallway light on the second floor was getting power but the three-way working from the top of the stairs at the dimmer down to the foyer three-way was not working properly. I also found that the fan has a short in the light kit which is causing the light to not work properly. The fan will need to be replaced because it is the harness itself that has the defect. We replaced the dimmer at the top of the stairs as well as the three switches at the front door. This repaired the issue with the second-floor light. While on site we check to see if we could move the thermostat in the second-floor hallway into the master bedroom on the wall above the switch. The wire is not long enough for us to relocate the thermostat which means the wire will need to be replaced. To do so the new wire will need to be wired into the furnace itself in t
We have installed a new gfci receptacle right outside the 2nd floor bathroom. In addition we have we have installed a new whole home surge protector at the main panel located in the basement.
This estimate includes the installation of a new feed wire to power the gate and post lighting in the front yard. We shall install new wiring in conduit, this new wiring shall be GFCI protected. We have determined that the post and gate lights need to be re-fed with a new wire, as we are unable to locate fault/break in existing wire. We shall return the 6/27/22 to complete work. We have installed a new wire from the house to the gate, creating a new feed. Original wire/feed was destroyed when a sprinkler line was installed. Our new wire has been installed in a conduit body.
WO-TNFR79281d Customer lost power to the 2 front outlets located under the front wooden banister and pillar next to the carport. I found that the GFCI under the banister had gone bad which didnâ€™t allow power to the other outlet. I replaced the GFCI and installed a new in-use cover and they both power back up. I also replaced the motion switch in the laundry room with a standard decor style switch. Light now turns on and off as it should. While on site i found that the 2 flood lights on the side of the home need bulb replacements (customer is taking care of bulbs).
Customers attic fan was not turning on. Replaced bad thermostat for existing attic fan. Installed new service switch for existing attic fan. Installed new attic fan in second attic section. Installed new service switch in for new attic fan.
Customer was having issue with Dryer breaker tripping constantly. I found loose connection on the breaker feeding the dryer circuit. I also found that there was several different brands of breakers in the BR series panel. We replaced all the mismatched breakers with the proper Cutler hammer BR series breakers.
Fished in new low voltage line to front of home and to doorbell chime to the top right of the front door. We ran low volt lines down to a transformer in the basement unfinished ceiling underneath the front door. Customer supplied doorbell, chime and transformer.
Top floor is original devices and connections are going bad. All devices were replaced and a GFCI breaker was installed on circuit due to there being no ground wire in circuit. Circuit has 7 receptacles, 4 switches and 1 dimmer. There is also an additional receptacle in dining room that needs to be replaced. Fan in master bed has power but the remote kit is no longer working and due to the style of receiver the fan has to be replaced. Verified proper operation of all completed work.
This estimate includes the replacement of the tandem breaker. The two bottom breakers were worn and cracked. We have replaced the bottom 2 breakers in the panel. Power has been restored.
Customers phone line in the kitchen stopped working. We found a buried junction box in the wall behind the cabinets. We ran a new line from the kitchen phone out to the verizon box on the back of the home. Line is now working again.