Troubleshooting basement lights not working. Found two broken single pole switches and replaced. Found mix matched circuit breakers in panel box.
Flood light repair and replace. Tech repaired and replaced motion flood lights with new flood light fixtures and LED bulbs
Boat Dock inspection. GFCI protected outlets and lights
customer called and said outlets were not working, electrician went out and diagnosed and replaced outlets.
Running new wiring to gate
Repairing and replacing landscape lights, wiring, timers and photo cells.
Replaced arc fault breaker that would not trip. Kitchen outlets are not working. Found GFCI was bad. Kitchen light is flickering. Found ballast was bad. Replaced t8 2 lamp ballast in fixture.