Alarm Systems Emergency Service Call Troublshoot pullstation going into alarm. Inoperable Deficiency for Edwards E-FSA Electrical Room: Arrived and pull Station had a broken toggle switch due to a controlled fire drill. Took device out and looped the wires together and deleted Device in panel to have a Normal. Need to return with pull Station to replace a re-add Device To Fire Alarm panel.
Portable Extinguishers Inspection Annual portable extinguisher inspection (2) (per unit + TSC)
Conducted annual fire extinguisher inspection
Alarm panel kept saying low battery. Technician replaced batteries.
Sprinkler Riser #2 in maintenance shop leaking. The drain is shut-off to the alarm line that goes to bell and out.
Survey area to install sprinkler heads in new addition
Disable and power down Simplex alarm panel.