While I did receive an email telling me ASA was coming, it was the morning of the visit. I would love to have a little more notice if possible. The tech was very easy to work with and knowledgable of our location. He makes it easy.
Alarm Systems Inspection Repair
Backflow Inspection Annual inspection of backflow devices. Inoperable Deficiency: Backflow Pit was flooded upon arrival. Water level was higher than rubber boot height. Will need to be pumped out to test.
Alarm Systems Service Call
Installed external antenna. Had to troubleshoot Telgard due to it being deactivated from the Verizon.
Alarm Systems, Emergency / Exit Lights, Sprinkler, and Portable Extinguishers Inspection Fire-Lite Sensiscan 2000 Electrical Room: Annual alarm inspection Annual E Light Inspection Reliable DW: Annual wet sprinkler inspection Annual portable extinguisher inspection BRC ID: 115742 Inoperable Deficiency: 1 5lbs CO2 due for Hydro (2012)
Sprinkler, Alarm Systems, and Portable Extinguishers Inspection Annual dry sprinkler inspection ***Check to see when next full trip test is due and note on your daily log Annual alarm inspection 6 Manual Stations 3 Photo Detectors 1 Waterflow Switch 1 Supervisory Switch 1 Sprinkler Tamper 7 Strobes 19 Speaker Strobes Annual portable extinguisher inspection (3) BRC ID: 368749 Annual sprinkler inspection
Conducted annual fire extinguisher and emergency/exit light inspections