ASA and Luis are always very professional and handle things in a timely manner. They also help out when your in a pinch and need things done very quickly. I’d recommend ASA to anyone who needs an excellent quality service.
ASA provide expertise, engineering, and full knowledge of a very complicated system all at a very competitive price.
Good quality work. Slow to complete project. Some delay due to my company changing specifications.
Excellent communication on setting up scheduled appointment and being on time as scheduled.
we will be having ASA do more service in our plants
Great service as usual. Paul always takes care of me. Thanks, Johnny
Backflow Inspection Please call Randy once onsite on 3/6 to let him know if can be completed since issue from 3/3 Mobile:404-673-2852
Annual Domestic Backflow Inspection (qty 3) Missing info on city's BF letter (uploaded below) 1. 1" 2. 1" 3. 1.5" Backflow Inspection Inoperable Deficiency: Wilkins 950XL failed due to having 2nd year cock broken needs to be repaired/replaced Inoperable Deficiency: Located two other yard boxes with no BF devices in them. According to Mr. Taylor the water lines are new. The location is properly marked with blue water marks and clearly visible. Need to check with the County to see if the devices were taken out.
Investigate the run-away short on the SLC.
Annual backflow inspection of (3) units 1) Febco 805Y 3/4" SN# No tag Location: Fire vault right of entrance next to sign 2) Ames 3000 6" SN# L30192W1012 Location: Fire vault right of entrance next to sign 3) Watts 007M1QT 2" SN# 135358 Location: Fire vault right of entrance next to sign Backflow Inspection
The quote below is for the annual inspections at W.R. Meadows of Georgia. Sprinkler, Backflow, and Fire Hydrant Inspection Annual inspection of (1) wet and (1) dry system Annual Backflow Inspection (6) Annual Hydrant Inspection (1) Deficiency: Main office building walk through: -2nd level hallway head needs adjusting Deficiency: Dry system building: -Adjust 2 escutcheons in office -missing escutcheon break room -Missing escutcheon men’s bathroom
Annual portable extinguisher inspection BRC ID: 491153