Great service took care of all our needs.
Alarm Systems and Foam System Suppression Service Call
Backflow Inspection Annual inspection of backflow devices. Inoperable Deficiency: Sprinkler Backflow Pit is filled with water . Will need to be pumped out and tested. Inoperable Deficiency: Back Flow Device Watts 007M1 QT DC SN:181954 failed both Checks at 0.0. Will need to be rebuild and tested.
Portable Extinguishers Inspection Monthly Inspection of Portable Eye Wash Stations (22) Monthly Pro-Inert and CO2 Cylinder Gauge Check Monthly 3-rotation of Post Indicator Valves (2). Must be recorded in Building Reports Monthly Fire Extinguisher Inspection BRC ID: 372672 (Send report with invoice) Monthly Inspection of Emergency Lights & Exit Lights
Alarm Systems Inspection Annual fire alarm inspection (all buildings)
Portable Extinguishers Inspection Inspect fire extinguishers in vans. Vans are back at facility by 4pm.
Alarm Systems Service Call Need to replace Vigilant VPS smoke detector in Room 38 that is going bad.