ASA has always provided our company with fast, reliable service. Their technicians are always professional and personable. Today we had the pleasure of meeting Troy. He was efficient and discovered our issue rather quickly. Thank you ASA!
Alarm Systems Inspection (1 day - 8 Hours)
Alarm Systems Inspection
Alarm Systems Inspection Annual inspection of fire alarm system and bar code set up (3) While doing the inspections we need to do a survey of the Fire alarm panel integrity. Several panels are hanging and several devices are located in undesired location. Need to take pictures of all fire alarm equipment so a quote can be generated. Inoperable Deficiency: Results from surveying while performing fire alarm Inspections; Complex has two primary fire alarm panels on building’s 1 (Monitoring 1-6) and 7 (Monitoring 7-14) which monitor each other. The ID’s on both are vague and need to be addressable. If a pull station on on either building’s FACP is activated; FACP only shows “Building pull station” but no location. Recommend programing maintenance to give specific location on activated pull station. All building’s only have 2 pull stations on the first floor. None of the other floors have pulls stations at stairs. Recommend pull stations on all floors to give all tenants an opportunity
Building 4: Investigate trouble on panel.
Portable Extinguishers Inspection Annual Fire Extinguisher Inspection BRC ID: 691852
Portable Extinguishers Installation Install 4" x 18" Rigid Plastic Extinguishers Signs at all units (bill per sign + TSC)
New TV & TV downstairs were not scrolling thru customers message. Got a TV that was working and connected it to the wiring where the TV's were not working and the message came right up and starts scrolling. Looks like the RGB connection has gone bad on the TV's.
Rebuilt check 1 valve on backflow
Conducted annual backflow inspection
Conducted annual fire extinguisher inspection
Service call for several emergency signs and lights that are not working.