Ken is always prompt and efficient. Great guy and services our facilities in a business like manner.
Tech is friendly and polite. Does his inspection-gets signature-and is on his way.
Mr. Howerton was very professional and knowledgeable. He passed along information to me that I was unaware of and offered any assistance that I may need in the future.
Alarm Systems Service Call
Annual Portable Extinguisher Inspection
Annual Fire Extinguisher Inspection (Appx. 10)
Portable Extinguishers Repair - (3) 10lb CO2 fire extinguishers due for hydrostatic testing - Need to install (3) new 10lb ABC fire extinguishers in the new warehouse
Annual portable extinguisher inspection
Portable Extinguishers and Sprinkler Inspection Annual Fire Extinguisher Inspection Annual Sprinkler Inspection Inoperable Deficiency: Riser’s 1/2 are due a 5 Year Internal Obstruction Investigation and Gauge Replacement x4 (1975/1999/2010) Control valves not locked or monitored. Missing Escutcheon ring in front office Missing FDC Sign Industrial size warehouse only has 5 10lbs FX which are all altered in Year. Will need to replaced those. Recommend a survey for additional fire extinguishers as it does not have adequate fire extinguisher coverage for the size of the building.
Portable Extinguishers Installation Deliver and Install Fire Extinguishers. They do not have any and do not know what size or how many they need.
Below are the deficiencies following the recently completed 2018 annual inspection: Portable Extinguishers Repair Fire Extinguisher Repairs. - Need to replace (1) 10lb ABC fire extinguisher with a new unit.
Below are the deficiencies following the recently completed annual inspection: Portable Extinguishers Repair (15)-10lb Abc due for 6 year maintenance (19)-10lb Abc due for hydro test (1)-10lb Abc new (1)-5lb Abc recharge (1)-2.5lb Abc new