still waiting for the information regarding the part needed information to fix the display panel.
Will need to reschedule for Dec 10. Customer will let guest know that we will be setting off alarms this day. Giving us the opportunity to troubleshoot the Mic
Deficiency: Maintenance alert smoke detector top of elevator shaft Deficiency: 3rd floor speaker circuit open. The wire is damaged or a device has been taken down
Annual Emergency / Exit Light Inspection Annual Fire Extinguisher Inspection BRC ID: 698450
Replace 10lb ABC that was used in a fire in front of building
Replace (5) cabinet doors that have fallen off due to high winds.
Replaced 5 10lb extinguisher cabinets, added 1 5lb extinguisher, 13 10lb extinguishers, recharged 1 10lb extinguisher
Recharged fire extinguisher that was discharged
Annual fire extinguisher inspection
Annual Fire Extinguisher Inspection