Service work to be quoted: (26)-10lb abc due for 6 year maintenance (2)-10lb abc due for hydro test (1)-10lb abc recharge (1)-10lb abc new (4)-5lb abc due for 6 year maintenance (3)-5lb abc due for hydro test (2)-2.5lb abc new (3)-10lb co2 due for hydro test (1)-5lb fe36 due for 6 year maintenance
Annual Security Fence inspection. Includes visual only inspection for coverage and condition, including gap from ground level. This is for main location at 14187 Nisshinbo Drive only. Annual visual inspection of perimeter lighting of building and street lighting in parking lot. Includes verification of light turning on and is for main location at 14187 Nisshinbo Drive only. Annual hand-held radio coverage inspection. Includes verification of radio coverage between units from one end of the facility to the other. This is for main location at 14187 Nisshinbo Drive only. Annual Portable Extinguisher Inspection (145) per NFPA 10. BRC# 707019 Annual Emergency/Exit Light Inspection (167) per NFPA 101. Annual Eye Wash Station Inspection (20) Annual AED Inspection (2) Annual Fire Door Inspection (8) per NFPA 80/1010 - includes replacement of fusible links Monthly Safety Inspection including Portable Fire Extinguishers, Emergency/Exit Lights, Eye Wash Stations, and AEDs. 2018 PO# 57565 BRC
Alarm service Call AFP-200 is not working. Replaced batteries yesterday batteries quit working today. Advised that the circuit breaker makes a weird noise.
Access Control Installation
Alarm Systems Service Call
Alarm Systems and Distributed Communications Inspection Annual Fire Alarm System Inspection (1) in NAMI1 per NFPA 72. Annual Fire Alarm System Inspection (1) in NAMI2 per NFPA 72. Annual EVAC/PA Inspection (1) per NFPA 25 Inoperable Deficiency: NAMI 2 Power Supply Above FACP had AC and Battery troubles prior Inspection. Need to investigate and repair. FACP and FCPS Batteries have no Dates and need to be replaced (12v/7amp).