ASA made an appointment right away. ASA showed up on time and provided professional staff to evaluate our needs and get the work done.
Annual portable extinguisher inspection BRC ID: 115757 Annual E Light Inspection Portable Extinguishers and Emergency / Exit Lights Inspection Inoperable Deficiency: 1 5lbs CO2 is due for hydro (2014). Need to return for a swap.
Annual Fire Alarm Inspection Alarm Systems Inspection
Service Call - Fire Trouble - waterflow
Install (6) 10lb ABC fire extinguishers Annual fire extinguisher inspection (3) Portable Extinguishers Inspection
Panel is bad it either got hit by lighting or a power surge. Panel has no 24v power. This causing the doors not to hold and was the reason the ac was not running. I added a MR101 to a NAC circuit to get the AC running.
The quote below is for the Annual Alarm Inspection of different systems: Alarm Systems Inspection Annual Alarm Inspection (Edwards) (2-systems) Inoperable Deficiency: Upon Arrival FACP appeared to be normal and LED Was functional. Upon opening panel door the screen went blank. Checked all wiring and all was correct and connected. I set off several fire alarm devices and FACP acknowledged it but would not read on screen, as far as location and type of device. Signals did go to Monotoring station. If a fire device goes off location and type of device will not known. System will be red Tagged. Particular panel model is no longer made. Spoke with management and they advised that they had the same problem and panel screen was replaced.
Backflow Inspection Annual inspection of 1 Backflow for $75. If multiple backflows are found, they are an additional $50 each. Backflows are required to be tested annually. All paperwork is handled by ASA and sent to the Utility company.
Portable Extinguishers Inspection Annual Extinguisher Inspection
Annual Extinguisher Inspection BRC ID: 691016
Annual Portable Extinguishers and Kitchen Suppression Inspection
Portable Extinguishers and Emergency / Exit Lights Inspection
Conducted annual fire extinguisher and emergency light inspections