Bert, Mike and the whole crew that came out to take care of our facility were both fantastic.
Sprinkler Inspection Annual Sprinkler Inspection for K building only - 1 wet riser and 4 units Inoperable Deficiency: System is shut off. Will need to investigate as to why it’s shut and will need to air pressure test to see if ok to refill. Water Flow Device is not connected to any alarm nor electric bell. Gauge is dated 2012 and will need To be replaced. Riser is located in rear bedroom closet of apartment 4 in Building K. SYSTEM WILL BE RED TAGGED.
Alarm Systems Service Call
Annual Fire Alarm Inspection Alarm Systems Inspection
Tech will perform initial Fire Alarm Inspection Alarm Systems Inspection
Sprinkler and Alarm Systems Inspection Annual Sprinkler System Inspection Tech will perform initial Fire Alarm Inspection
Alarm Systems and Sprinkler Inspection Annual Fire Alarm Inspection Annual Sprinkler Inspection (3) Inoperable Deficiency for Vista & Firelite Vista 20P with a 32FB & MS9200: FACP had an active Comm Fail and DACT Trouble prior Inspection. No signals went to monitoring station during Inspection. Need to investigate to see if it’s a dialer or phone line issue.
Portable Extinguishers Inspection
Conducted annual sprinkler inspection
Conducted 5 year internal obstruction investigation on sprinkler systems