Annual inspection of portable fire extinguishers Portable Extinguishers Inspection
Alarm Systems Service Call
Downgraded micro codes. Tested Proinert. Will need to be back tomorrow to seal all conduit and seal all pull stations in Plant.
Bypassed CRH going to the T300 for the Turbine Trip. Closed the contacts so the T300 could be at its normal state. Spoke with Robert about the relay, so we could rule out if it’s a Card or relay issue. Contacted EST about the timing issues and was told they are still working on it. Will need to be back out here Wednesday afternoon to check status of T300. Will also need to bring the locks to replace existing ones.
Replace the existing silent knight 5207 fire alarm panel.
Responded to Duct Detector Alarm in Men's Restroom. Arrived on site checked Duct Detector filter is clean. Adjusting sampling tube. Cleaned out Duct Detector. Panel normal upon departure
Arrived on site went through history found Ground Fault on Low Pressure on Bottles on Unit 2. Found wire moist with condensation. Taped wire and siliconed wire to avoid future problems.
Upon arrival panel had Unit 2 Electrical Package OFF BOTTLE Trouble. Went to unit 2 EP checked wires with meter. Reterminated all connections. Went to Unit 2 Excitation. Could not get Module to clear. Replaced module, check wired with Meter. Panels have 2 Troubles upon departure. (Panel 3 and Panel 4)