Bert is by far the most professional service rep. Always on time, communicates issues, and gets the job done. Thank you!
Kenneth was very pleasant to deal with and showed interest in what we do here. He will always be welcome. And we need a price on another 5 lb CO2. Thank you.
So far the exchange of problems and answers has been very good. Will know more when job is completed.But so far every thing is falling going good.
I have used ASA for years. They are polite and professional. They know their stuff! I will use them for years to come.
Technician arrived on time and was friendly and clearly explained before and after the inspection what was happening. Thank you!
Justin did a great job, very helpful and professional!!
Annual Sprinkler Inspection (1 wet/1 dry) in PLC Building Annual Hydrant Inspection and Flow Test per Cobb County requirements. (2-Hydrant Flow Test and Site Map) Investigate the Tamper Valve Sprinkler and Fire Hydrant Inspection Inoperable Deficiency for Ready Riser: Tamper switch at outside PIV of Sanctuary needs to be replaced. After wire disconnection trouble stayed the same.
Annual Sprinkler Inspection (1-Wet) Sprinkler Inspection
Portable Extinguishers and Emergency / Exit Lights Inspection Annual portable extinguisher inspection BRC ID: 115558 Annual E Light Inspection
Alarm Systems Emergency Service Call
Alarm Systems Inspection
Bldg 2 has no power . Investigated issue found bad breaker needs to be replaced by electricians asap. Then we will need to replace batteries because they have been drained by a/c loss
Alarm Systems Service Call