Technician quickly identified source of problems and made repairs in a safe and efficient manner.
Alarm Systems Inspection Below is a quote to complete the Effingham County Fire System Inspection
Alarm Systems Inspection Inoperable Deficiency: Smoke Detector in Plant Water Analysis (Sampling) Room needs to be replaced (Siga IPHS) Smoke detectors in Admin Office Hall, Control Room, and Control Room Hall need to be replaced. After several cleaning attempts they would not clear from alarms that were there prior to inspection. (System Sensor 2WB). There’s one More Fire Alarm panel that needs to be inspected (Chiller Mod) that was powered down due to outage. Need to return and inspect it. Below is a quote to complete the Effingham County Fire System Inspection Annual Fire Alarm Inspection
Sprinkler Inspection Below is a quote to complete the Effingham County Fire System Inspection
Conducted annual sprinkler inspection and replaced missing head wrench from spare head box
Annual Fire Extinguisher Inspection