Need to investigate devices that may have been missed during the new install. 2 Paint booths on the 3rd floor and 1 Dry system on the 2nd floor. Both have older looking modules on them. Need to see what is needed to replace those. There was also a ground fault on the new system Need to investigate.
FACP for the main buildig had a FDLC 1 DLC Short trouble prior to arrival and annual fire alarm inspection. None of the devices activated the fire alarm panel. Spoke to management and they advised that they were aware due to their electrician notifying them. Need to investigate system to locate issue and repair if possible or quote additional repairs if needed. Following investigation and repair, re-inspection of the system will need to be completed. - repair
Troubleshoot Annunciator loosing communication with the FACP.
Alarm Systems Inspection Annual Fire Alarm Inspection (2) Inoperable Deficiency: FACP Had a “FDLC 1 DLC Short” trouble prior my arrival and Inspection. None of the devices activated the fire alarm panel. Spoke to management and they advised that they were aware due to their electrician notifying them. Need to investigate and repair. The Re-Inspect.
Emergency / Exit Lights and Portable Extinguishers Inspection
Monthly Fire Extinguisher Inspection. PO# 4550432483 Monthly SCBA Inspection. PO# 4550432483 Repair work
Conducted monthly fire extinguisher and scba inspections
Conducted monthly extinguisher, SCBA and fire door inspections
Conducted annual fire hydrant and alarm inspections
Made repairs to the foam sprinkler system