Troy came out in the middle of the night to address an issue. It was a long drive but he was pleasant and professional when he arrived and was able to quickly diagnose the problem.
Alarm Systems Inspection Ademco Vista-128FB Electrical Room - Building 1: Annual alarm inspection (5) Inoperable Deficiency for Ademco Vista-128FB Electrical Room - Building 1: Building 5 Water Flow and and Pull Station Near Riser did not activate Fire Alarm. Need to investigate and repair. Building 3 Upon audio visual inspection it was discovered that non of the Horn Strobes functioned upon Fire alarm Activation. Need to investigate and Repair NAC Circuit To Fire Alarm Panel.
Low Voltage and Alarm Systems Repair
Low Voltage Repair
Alarm Systems Repair
Service Call - Investigate Alarm issues and troubles on panel - onsite contact is Janet Clark - 770-271-8228 Bldg 1 - Ground fault every time it rains Bldg 2 - Zone 20 - Alarm right rear entry door, the alarm goes off every night Bldg 4 - Trouble on panel - Periodic test with system trouble Bldg 5 - Zone 41 - Pedestrian door - the motion detector keeps false alarming and Janet would like it removed.
Alarm Systems and CO2 Suppression Inspection Ademco Vista-128FB Electrical Room - Building 1: Annual alarm inspection (5) Recharge Paint Booth System that was dumped
Alarm Systems Emergency Service Call Fire alarm is not turning off after alarm went to monitoring for water flow
Annual portable extinguisher inspection BRC ID: 114622
Annual portable extinguisher inspection Semiannual wet chemical hood inspection