There was some internal confusion ... meaning I did not know Cody & Wally were coming this morning. They introduced themselves ... and what they were hare to do. Very professional ... did they work ... caught me up to speed from their end. Work completed (understand this is not a big job / account) in a timely manner. All good! Cody gave me his business card.
It's your job to show up on time, do what you're there to do and be polite to the customer; there's a few that see that as just the basics and go on to excel from there. Aztec Fire is like that. In the years we have used this company, the service is always superlative. Thank You!
Thank you for making sure we are safe with well serviced fire extinguishers.
Cody was very professional on time and very knowledgeable.
Good work quick and polite
Portable Extinguishers Inspection
Portable Fire Extinguisher Inspection
5# new fire extinguisher for R&R, per Chris price is $58 dollars + tax.
Portable Extinguishers Inspection Annual Fire Extinguisher Inspection
Portable Extinguishers Inspection Congatec - EXT 4: Annual Fire Extinguisher Inspection.
Portable Extinguishers Inspection FSC Coatings - EXT 4: Annual Fire Extinguisher Inspection Deficiency for FSC Coatings - EXT 4: (2) Extinguishers In Ware house are hung up over 5 feet customer was advised. Customer said he will fix the discrepancy. Customer is responsible. (1) 10lb abc Inside break room needs new bracket installed, customer also responsible No quote needed.
Portable Extinguishers Inspection STATRAD - EXT 8: Annual Fire Extinguisher Inspection
Portable Extinguishers Inspection Jimbos El Camino - EXT 9: Annual Fire Extinguisher Inspection Deficiency for Jimbos El Camino - EXT 9: Customer says he will lower fire extinguisher inside meat department to meet the code of no higher then 5Ft Customer is responsible
Portable Extinguishers Inspection Main Building 44: Annual Fire Extinguisher Inspection
Alarm Systems Service Call Service Call: Fire alarm panel is beeping, please troubleshoot. Called in by Mike (619) 654-7963.
Sprinkler Inspection Fire Control Room: Quarterly Fire Sprinkler Inspection
Portable Extinguishers Inspection Deficiency: Customer requested a quote to replace (11) 8x18 cabinet glass, due to installing tempered glass, with no breaker bars -Locations - Building 3310 replace tempered glass by unit 304 - Building 3310 replace tapered glass by unit 302 - Office / Community room plexi needs to be change - Building 7260, by unit 204 - Need to replace 8x18 tempered glass with plexi and breaker bar - Need to replace glass with plexi by unit 301 - Building 7255, by unit 102 - Need to replace glass with plexi - Need to replace glass by unit 202 - Need to replace glass by unit 304 - Building 7239 damage plexie needs to be change by unit 301 Customer requested a quote to replace (94) 5lb abc fire extinguishers that are due for hydro static testing, shall be replace and or hydro - see report for locations Annual Fire Extinguisher Inspection
Scope: Replace (15) 5 lb ABC portable fire extinguishers Replace the glass on (13) portable fire extinguisher cabinets Perform the 6 year tear down on (9) portable fire extinguishers Qualifications: Excludes any additional repairs, if needed Portable Extinguishers Repair Customer has requested a quote to perform (9) 6 year tears downs, due to being pasted due to leaked by previous venders - Locations - by unit 25 - by unit 27 - by unit 73 - by unit 75 - by unit 186 - by unit 163 - by unit 101 - by unit 88 - maintenance garage Customer requested a quote to replace (13) 9x24 cabinet glass, due to being broken / missing - Locations - by unit 92 - by unit 14 - by unit 12 - by unit 45 - by unit 41 - by unit 19 - by unit 31 - by unit 110 - by unit 108 - by unit 104 - by unit 171 - by unit 162 -