Kyle and his team were great, and completed 1 floor of sprinkler head changes in 1 day! Great Job!
We do not have your billing yet. So I will not answer rating costs yet. You have been good in the past years.
Haven't received the bill yet, can't rate the cost of the service.
VERY KNOWLEDGEABLE , SHOWED UP WHEN SAID HE WOULD BE THERE
Response from Confires:
Russ, Thank you for taking the time to acknowledge Dave. All of our technicians strive to ensure that our customers are pleased with our service. Please feel free to reach out to me directly if Confires can be of any further assistance with your fire protection needs. I can be reached at 908-912-3060. Thank You, Mark Calleo Vice President & General Manager
Liugi was professional, courteous and helpful with our request. Great job!
** JOE M 732-287-4880 ** Confirmed appt with John P (Heller / landlord) 732-710-5367 also confirmed appt with Frank via email - 732-403-3783 tech to arrive at 8am The following discrepancies were found during your Annual Sprinkler Inspection that needs to be corrected for Compliance: 5 year internal inspection is due on (6) wet riser and must be completed per NFPA 25.. Need to replace (5) outdated water gauges. System 8, could not perform pressure test due to main line pipe and 2" elbow broken at threads. Will need to replace 2" down drop (threaded) and 2" elbow. Fire Hose inspection performed and completed at this time. (12) Fire hoses inspected. Found (3) fire hoses needing hydro. NOTEThis quote is priced out for the hydro test on (3) hoses. If hose fail hydro testing. We will send you a follow up quote pricing for replacement hoses. NOTE SCISSOR LIFT NEEDED Sprinkler Repair
Special Hazards Inspection