Not only did they follow up. The were here as scheduled and went over details on how to use properly.
Thanks so much for your excellent service and for discovering a serious problem with the Exit lights. I appreciate all your help and suggestions for solving the problem.
The Gentleman was friendly & completed the inspection in a timely manner.
Excellent and Very professional service!!
On site to perform 3 year pressure test and 5 year internal inspection of (2) dry systems.
*** MATERIAL ON STAGING SHELF *** Confirmed appt wit Andy 908-754-8180 Tech arrival: 8:30am The following discrepancies were found during your Annual Sprinkler Inspection that needs to be corrected for Compliance: DRY SYSTEM As noted during the investigation for leaks. The dry pendants are from 2005 suggest replacement of dry pendants as they are over 10 years old. Price includes approx 8 new dry pendent heads to replace the 15 year old dry heads. 3 air/water gauges are outdated WET SYSTEM 3 gauges for sectional valves are outdated Sprinkler Repair