Work was done quickly and efficiently.
Great service. Would recommend
Sean and his partner were great to work with.
I was please with the service work that Sean provided
Inspection dept: kitchen semi-annual inspection Inspection dept: Extg Annual inspection
Sprinkler Repair Confirmed appt with Scott via email - 908-301-5626 Email: SClark@lindabury.com Tech arrival: 10-12pm Performed the 5 year hydro test on the fire department connection. Results was a failure as the FDC did not hold pressure for two hours. Leak is on the 4” pipe inside of the wall repair should be performed to correct. Material needed: (1) 4” groove x flange adapter 5’ of 4” pipe sch40 Threaded and one side. (Tech need to fabricate the piece on site) 1- Siamese connection.
Semiannual Inspection Dept: KITCHEN Equip Desc: Inspect Kitchen Fire Suppressi Alarm Int: No