Tony was great. Trouble shot our short cycle compressor problem , replumbed connections, plus cycling adjustment. Confident with this experience.
Upon arrival found air line closed however system did not lose any pressure. Compressor was short cycling how ever no pressure loss was indicated. Adjusted cut in and cut out on pressure switch to observe if this was the cause and did not fix the problem. Disconnected entire air line piping assuming there could have been a leak at the trim replaced 1/2" ball valve and 1/2" nipple 4" long and tightened packing on all valves. After doing the following things noted spent time on site to be sure the problem was solved. At this time system is in service and compressor is now functioning properly. Upon departure all systems normal