Jared came back to my property to install all our new fire extinguishers in our end rooms. Jared was fast but very efficient getting the job done. Jared was friendly and knowledgeable once again during the install. I will recommend you all for years to come!
Zack was fast and polite. He knew what he was doing and had no issues completing the work.
I've used Fire Pros for alot of work for our old facility - and they've been great and provide excellent service everytime.
We had our annual fire extinguisher inspection today. It is always a pleasure to have this completed by Jared. He is extremely knowledgeable and efficient.
No air in the dry system, compressor had failed. Temperature was 19 degrees. Drained all piping as possible to reduce further damage from freezing. Placed system is a stand-by status until repairs can take place.
Once again Alex provided great, professional service with a smile. Much appreciated!
Very friendly and professional
The service Technician, Matt, was very courteous, and very thorough in explaining what needed to be done today, what was done/replaced, and what needs to be done in the near future as far as expiration dates are concerned.
Arrived On-Site Central Station states there getting Zone 01 Main Entrance Pull Station Troubles trips and Resets. FACP Normal upon Arrival. FACP History states Zone 001 M33 M016 (Supervisory Switch Tbl and Rst) which is not the Main Entrance Pull Station. After further investigation found a set of NAC Panels and Silent Knight SLC Extender Panel in 218 Hall Electrical a Room Found Top Fire-Lite NAC Panel batteries Required Replacement. (Replaced 2-12 volt 7 batteries)Found On SLC Extender Panel in 218 Hall Electrical Room (Addresses on Panel are 10-17) 16 was strapped out and not in use which is also the same point that was going in and out of trouble. Found that the resistor was not properly seated and was going intermittently in and out of trouble. Re-Fastened resistor and reset System, also updated date and time on FACP. ***All Systems Normal and Reset ***
Arrived On-Site M002 Rear Pull station was in Alarm on FACP Checked Pull station, Handel was reset but switch inside was not returned to normal position. Flicked switch up to normal position and reset pull station. Also tested both front and rear pull stations they both function properly. Also explained operation of Fire Alarm system and how to reset. ***All Systems Normal and Reset ***
Portable Extinguishers Repair
**Border Foods** Semi-Annual Kitchen Suppression Inspection
Semi-Annual Kitchen System Inspection Range Guard 2.5 gallon
Completed annual Fire Alarm inspection for 2020