We send a lot of work orders to Fire Protection Service, and they have done work in a timely and quality manner. 10/10 Would recommend!
I was able to schedule quickly and get the stuff done that needed to be done before I was out of office. They explained everything and made sure everything was back to normal before leaving.
easy to work with
hardworking and very polite and knowledgeable
Emergency / Exit Lights Inspection
Monthly Post Indicator Valve Inspections 2019 - PO# 40458508 / Item# 00030
Alarm Systems Repair Batteries in the 4th floor panel are bad and need to be replaced. # @ 12 volt 18 amp hour are needed. Nut and bolt style. Ep-SLA12-18B1. - repair
FACP FRONT LOBBY (7818): 47 SMOKE DETECTORS FAILED SENSITIVITY TESTING AND NEED TO BE REPLACED. CAN BE REPLACED WITH MODEL 2WB. SEE SENSITIVITY REPORT FOR LOCATIONS. - repair
Original quote was for only (1) combo light and (4) batteries. There was (1) additional combo light that needed to be replaced per inspection report. Talked to Rick Mol and he gave me approval to add that to the quote told him it would be additional $210.
Annual Fire Extinguisher Inspection of 196 units
Annual Fire Extinguisher Inspection (18 FE)
Replaced and Tested 4-Expired Smoke Alarms that were Deficient from recent inspection. ***All Systems Normal and Reset ***