very personable, very knowledgeable, and explained everything
Sean was very nice to work with very professional and personable.
Gary did a great job as always! Thanks!
Quote for Building D: The Bell/Strobe in the office is not part of the current Fire Alarm system and needs to be removed and a 4x4 cover put over the box, Replace a non-working Horn/Strobe in the TV room - repair
Inoperable Deficiency: horn strobes in 2nd floor hall from by Rooms 203 - 242 failed to function properly. The horns worked and the strobes did not. I suggest we send a technician to troubleshoot the line of horn strobes
Corrected Deficiencies from Recent Inspection Replaced 20- 12 volt 18 ah batteries and 11-12 volt 7 ah batteries ***All Systems Normal and Reset ***
Biennial Smoke Sensitivity Testing (every 2 yrs)
9.5 Lb FE-36 SWITCH ROOM: Annual Fire Extinguisher Inspection.
Semi-annual Special Hazards Suppression System Inspection.
Kitchen Suppression and Portable Extinguishers Inspection
Annual Fire Extinguisher Inspection
Semi-annual Special Hazard Inspection.
Annual Fire Extinguisher Inspection (11 FE)