He was very through on making sure that everything was up to par.
would recommend to others
The technicians are always so friendly and let me know each and everything they are going to test before they do the test.
Very friendly and knowledgeable
He was quick and very professional.
Tech showed up 2 hours after appointment time and caused me to stay after work about 2.5 hours because the job also took longer than estimated.
Very fast response
Sean did a good job. He should bring donuts the next time. lol
Completed Emergency Sprinkler Service Call
1)Replaced Inner Front Door Key Pad Completely (New Key Pad, New Wire Harnesses and Used New Static Shock Wiring Harness. Re-Wired, Programmed and Tested Key Pad. *** All systems Normal and Reset *** 2)Replaced Foyer Vestibule Key Pad Mother Board and Installed Static Shock Wire Harness. Programmed and Tested ***All systems Normal and Reset *** 3)Replaced Door Contact on Inner Front Door. Wired and tested.
Repaired the horn strobe by the technology room exit door.
Fire Door Service Call
Wet Basement storage: Install the missing Inspection Test Valve sign and provide proper identification. Valve identification is beneficial in at least three ways. It allows the fire department personnel to locate and operate the valve. A contractor can readily shut off the system to make modifications. And system valves can be easily identified during periodic inspections. NFPA 13 (184.108.40.206) All control, drain, and test connection valves shall be provided with permanently marked weatherproof metal or rigid plastic identification signs. Wet Basement storage: Remove and replace the outdated water gauge. Pressure surges are typically trapped in the system by the check valve. Readings from these gauges can be used to establish a database on the available pressure in the water supply. The gauge on the supply side is also used during the main drain test to establish a database of residual pressure in the water supply. NFPA 13 (8.17.3) & NFPA 25 (220.127.116.11) Gauges shall be replaced every 5 yea
Installed new cellular communicator.
Completed Annual Fire Alarm Inspection for 2019
back plate is rusting on smoke detector that I just programmed the head for Point 19. I showed Demonte the rust forming,there will be issues in the near future with 19. I suggest it's replaced before troubles arise. customer had water damage in the area - repair
Annual Fire Alarm System Inspection
New 12 volt Power Supply Installed 1-17-19 ALR For Interior Key Pads ***All systems Normal and Reset ***