I had problems getting a vendor to service the site, I contacted Fire Pros and they responded quickly with a quote and scheduled service right away. To everyone at Fire Pros thank you for your help and quick response.
Suggested for SD ROOM 314: Room smoke detector in room 314 not working properly at this time. Head went into alarm on customer last week maintenance cleaned head to no avail. I cleaned smoke detector head very thoroughly and still went into trouble condition. Fire pros to ship Simplex smoke detector head to Jason he will install when received.
Deficiency: SD IN POOL AREA SOUTH IS SHOWING NO ANSWER. VERY CORRODED. AND COVER IS CRACKED. TERMINAL SCREWS ARE BOTH RUSTED BAD Deficiency: FACP SHOWING CARD 2 FAILURE, POWER SUPPLY/CHARGER. CUSTOMER WILL CALL SIMPLEX
do inspection on MRI trailer #596
wet systems 1, 3, and 5 due for 5 yr internal pipe assessment - repair
Painted and covered heads throughout store. - repair Repair of Heads too close together, recommend removing line.
Sprinkler, Alarm Systems, Kitchen Suppression, Emergency / Exit Lights, and Portable Extinguishers Inspection