I had problems getting a vendor to service the site, I contacted Fire Pros and they responded quickly with a quote and scheduled service right away. To everyone at Fire Pros thank you for your help and quick response.
Manual pull station in pool area was broken by guest and needs to be replaced - repair
Deficiency: Manual pull station in pool area was broken by guest and needs to be replaced
Annual Fire Alarm System Inspection
Annual Fire Alarm Inspection
Annual Fire Alarm Inspection on MRI trailer #596
Suggested for SD ROOM 314: Room smoke detector in room 314 not working properly at this time. Head went into alarm on customer last week maintenance cleaned head to no avail. I cleaned smoke detector head very thoroughly and still went into trouble condition. Fire pros to ship Simplex smoke detector head to Jason he will install when received.
Deficiency: SD IN POOL AREA SOUTH IS SHOWING NO ANSWER. VERY CORRODED. AND COVER IS CRACKED. TERMINAL SCREWS ARE BOTH RUSTED BAD Deficiency: FACP SHOWING CARD 2 FAILURE, POWER SUPPLY/CHARGER. CUSTOMER WILL CALL SIMPLEX
do inspection on MRI trailer #596