Very thorough, friendly and knowledgeable.
They both were very professional, and worked around my staff that was stocking.
The fire pro workers was very friendly.
Suggested: FACP BATTERIES SHOULD BE REPLACED. LEFT BATT HAS UNDER 12V AND BOTH DID NOT LOAD TEST WELL Suggested: FACP BATTERIES SHOULD BE REPLACED. LEFT BATT HAS UNDER 12V AND BOTH FAILED LOAD TEST Deficiency: Second-floor guest laundry smoke detector was painted over and needs to be replaced..can’t even get it apart. Smoke detector next to it is model # BASE: 4098-9788 HEAD: 4098-9757
change smokes on zone 3 - 7 total. WORKORDER NUMBER 37328517
24 hours after contractor reset the alarm it went off again and the fire department was called. Please fix the faulty sensors
Per Joe Magistri: Fire Alarm keeps going off - possible a bad sensor
do fire alarm inspection and reports on buildings Winimac, Shawnee and Iroquois.
Annual Fire Alarm Inspection
Painted and covered heads throughout. - repair Repair of Wet system piping due for 5 yr internal pipe assessment - do while changing painted heads - systems 1, 3, and 5
Painted and covered heads throughout. - repair Repair of ESFR in upright position. Repair of 7 control valves in pump room are not indentified.
Wet systems 1, 3, and 5 due for 5 yr internal assessment - must complete while changing painted heads - repair
Clean Agent Suppression Inspection