Very thorough, friendly and knowledgeable.
They both were very professional, and worked around my staff that was stocking.
The fire pro workers was very friendly.
repair ground fault on system.
EMCOR Paperwork Attached The fire alarm has gone off 4 times this week. Technicians were there on Thursday morning it was going off again. Zone three again. Is has had more than 25 false alarms in the last two years everyone in zone three. Replace the system or at least every piece of equipment in zone three. TO DO test all the smokes and be sure they display they trip and he can track the wire inch by inch to be sure nothing else is tied in.ED is quoting a panel replacement.LAST ITEM , switch zone 3 and 4 around, notify their monitoring station of the change , this way if it trips again we will know if it is the panel or the loop.
EMCOR Paperwork Attached The Fire alarm was sounding again, Sunday evening. Again it was a sensor in section 3 it has been a section 3 alarm every time it has gone off for two years now. Mike replaced 7 smokeless in the east hall a year ago. Please see if any latched ? Anything else tied on to that loop?
Manual pull station 3rd floor south. handle is broken and it needs to be replaced. model 4099-9001 - Also replace bad heat detector.
Suggested: FACP BATTERIES SHOULD BE REPLACED. LEFT BATT HAS UNDER 12V AND BOTH DID NOT LOAD TEST WELL Suggested: FACP BATTERIES SHOULD BE REPLACED. LEFT BATT HAS UNDER 12V AND BOTH FAILED LOAD TEST Deficiency: Second-floor guest laundry smoke detector was painted over and needs to be replaced..can’t even get it apart. Smoke detector next to it is model # BASE: 4098-9788 HEAD: 4098-9757
change smokes on zone 3 - 7 total. WORKORDER NUMBER 37328517
24 hours after contractor reset the alarm it went off again and the fire department was called. Please fix the faulty sensors
Per Joe Magistri: Fire Alarm keeps going off - possible a bad sensor
do fire alarm inspection and reports on buildings Winimac, Shawnee and Iroquois.
Painted and covered heads throughout. - repair Repair of Wet system piping due for 5 yr internal pipe assessment - do while changing painted heads - systems 1, 3, and 5
Painted and covered heads throughout. - repair Repair of ESFR in upright position. Repair of 7 control valves in pump room are not indentified.