Good quick service can always rely on Eric and his crew
Eric really cares and goes above and beyond! He is rare in this world today please keep him around!!!
Suggested: Smokes in attic are not up by ceiling. Only 2 of the 14 attic smokes are up near ceiling high point. To raise the rest would take extra wire added in to reach highest point. This would need to be quoted T and M. All smokes worked properly but most are to low (about 5’ high) from highest point in attic
EMCOR Paperwork Attached Annual Fire Extinguisher Inspection
Semi-annual Fire Alarm Inspection - SIMPLEX 4010 -137 DEVICES
FDC signage missing - repair
Annual Fire Extinguisher Inspection (11 FEs) Semi-annual Fire Alarm Inspection - SIMPLEX 4010 -137 DEVICES Semi-annual Fire Sprinkler Inspection (1 wet)
Kids were playing in the pool area with a soccer ball and hit a sprinkler head amd broke pipe inside as well.
Alarm Systems Service Call