The work that was done was professional and expedient. I was pleased as usual with Fire Pros
Great service! I really appreciate the time and attention given to helping me understand the system I newly inherited.
Response from Fire Pros, LLC:
Thank you for leaving a review, we greatly appreciate your feedback! Gerald is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Techs who made repairs did a great job, initially on 9/3 tech was unable to even accomplish a temporary repair.
got the job done quickly and was in and out almost before I knew it.
They came in and did the job without needing any help. They were quick and efficient.
Went well good job
Eric was more than helpful with everything he did. He not only took the time to explain certain things but he also went out of his way to make sure I understood what was needed. He also is going above and beyond to make sure our company is taken care of every way possible. He was amazing to work with.
Annual Fire Extinguisher Inspection of 11 units @ $42.23 Semi-annual Kitchen Suppression System Inspection (1) Pyrochem PCL-240 @ $61.80 changed (2) 360 links @ $10 ea
Clean Agent Suppression Inspection
Inspected Buckeye extinguisher
Replaced two Victaulic elbows, several Victaulic couplings and multiple sections of pipe.
4- Pump room: pulled and plugged 1 12 in chrome 286 degree dry pendant that was damaged and leaking - above grocery freezer - replace with new
Victaulic coupling on auxiliary drain for system 5 leaks. It is immediately behind the riser.
Inoperable Deficiency for 4- Pump room: pulled and plugged 1 12 in chrome 286 degree dry pendant above grocery freezer
Jim Pruit called stating - sprinkler head leaking all over produce in isle 8 - needs someone out asap