1/14 Requested by and confirmed with Nassar. Requests after lunch rush as usual. km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection (2)ABC's (1)K-Class Semi-Annual Kitchen Suppression System Inspection PyroChem PCL-460 (2)500 links (3)360 links (9)Nozzles Deficiency: Number of Systems failed : 1 Deficiency: Number of Extinguishers Left at Job: 1 Deficiency for PCL 460 rear wall: Improper protection over grill. Deficiency for PCL 460 rear wall: Gyro machine not completely under hood and un protected. Deficiency for PCL 460 rear wall: Electric non fuel source on gyro does not de energize upon fire system actuation. Gyro is plugged in outside of hood with extension cord. Deficiency: K-Class fire extinguisher is out of hydro date.