EXCELENT SERVICE AS ALWAYS
WAESOME SERVICE AS ALWAYS
TYLER GAVE EXCELLENT SERVICE..
they always take care of our jobs in a timely and professional manner, I never have any complaints on workmanship and they always try to explain the process so you have a better understanding of whats going on
4/16 Appt confirmed with Corbyn Geiger, the GM for this location will be on site at 8:00 AM, Ian Garner. Understands alarms in test and access to the alarm panel. EMailed team. km Customer called in for inspection. We show due in May because of recalled work orders. Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection Semi annual inspection of the kitchen system Annual inspection of the extinguisher Annual inspection of the e/lights Deficiency: Improper plenum protection in fryer hood. Deficiency: Pressure fryers are undetected. Deficiency: Improper nozzle height over fryers. Deficiency: Electric connections are made inside of automan. Deficiency: Expellant hoses and regulators are out of hydro date. Deficiency: Number of Systems failed : 1 Deficiency: 2 piece link holders are bent and need to be replaced (5). One scissor style link holder is aluminum and needs to be replaced. Deficiency: K-Class fire extinguisher has been discharged and is leaking ch