Very very unprofessional. Came in when we opened and threw his stuff on our counter , he stepped on our grill with his shoes and it was gross. Asked for a free sub at the end .
Great Fast accurate Service
I have been with my company for over a year now, and have had a lot of companies do service and different things to our building/machines. We believe in a correct way, an aesthetic way, and a safe way. We appreciate when Fire Systems of Michigan comes because they handle our building like its their own. Jered is an outstanding professional service tech. Thank you
Gerald did job today doing the inspection.
We have always had good service from Fire Pros. Your representatives are knowledgeable, friendly and thorough. Thanks
Matt was extremely professional and handled the inspection in a timely fashion.
Completed Annual Fire Extinguisher Inspection for 2021
2/9/21 Confirmed with Bill for Thursday. SM Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-D6 (5)500 links (8)Nozzles Deficiency for Ansul R-102 6 Gallon Wall behind hood: Ansul system is alarmed to strip mall. Test system alarms did not operate during system actuation.
12/23 12/10 NA at location, emailed store manager and Val of appt. km 12/9 No reply, scheduled and emailed area coach km 12/1 Emailed area coach km Portable Extinguishers, Emergency / Exit Lights, and Kitchen Suppression Inspection Annual inspection of the fire extinguishers Annual inspection of the e/lights Semi-annual inspection of the kitchen fire suppression system Deficiency: Number of Systems failed : 2 Deficiency: Number of Extinguishers Left at Job: 2 Inoperable Deficiency: Batteries in exit and emergency lights failed. Inoperable Deficiency: 1- 10# abc fire extinguisher discharged. 1- 6L K-Class fire extinguisher discharged Deficiency: Single tank system has improper protection over deep fryers. Deficiency: Improper protection over pressure fryers and deep fryers on main system. Deficiency: 1.5 Gallon tank out of hydro date and under filled. 3 Gallon tank out hydro date. 2- Regulators and 2 expellant hoses out of hydro date Main Hood Deficiency: Front Hood Regulator and h
12/8 Confirmed with Megan. No cooking at 9:00-9:30 km Kitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-S1.5 (1)360 link (3)Nozzles Annual Extinguisher Inspection Suggested for R-102 1.5G built-in end cap: Unable to verify building alarm and built In make up air shut down. Suggested: Store does not have any portable fire extinguishers.