TJ was great to work with and answered all questions. Arrived on time and made sure we were satisfied with the job before he left.
Technician was on time, knowledgeable and performed the work as outlined.
Work was conduction quickly and accurately. I appreciated their feedback.
Very very unprofessional. Came in when we opened and threw his stuff on our counter , he stepped on our grill with his shoes and it was gross. Asked for a free sub at the end .
Great Fast accurate Service
I have been with my company for over a year now, and have had a lot of companies do service and different things to our building/machines. We believe in a correct way, an aesthetic way, and a safe way. We appreciate when Fire Systems of Michigan comes because they handle our building like its their own. Jered is an outstanding professional service tech. Thank you
Gerald did job today doing the inspection.
We have always had good service from Fire Pros. Your representatives are knowledgeable, friendly and thorough. Thanks
Matt was extremely professional and handled the inspection in a timely fashion.
8/2/23 confirmed with Michael SM Portable Extinguishers Inspection Annual Fire Extinguisher Inspection (22 FE) Deficiency: Number of Extinguishers Left at Job: 7 Deficiency for 10 lb ABC Sanctuary staircase landing: Five 10# abc fire extinguishers due for 6 yr. maintenance. 4 Badger and 1 Kidde. One 10# abc and one 5# abc fire extinguishers (Ansul) leaked down after 6 yr. maintenance was done last year.
Notice of Non-Compliance and Repair Proposal Adams Fire Protection Co. recently inspected/serviced the fire sprinkler system at your establishment in accordance with NFPA Standard for Inspections, Testing, and Maintenance Requirements (2017 Edition). While inspecting/servicing your fire sprinkler system, it was determined to be "Non-Compliant". NFPA 25 (220.127.116.11) The property owner or designated representative shall correct or repair deficiencies or impairments. The attached proposal summarizes the deficiency/impairment issues that were found during the inspection/service and the costs and actions needed to correct them. Adams Fire Protection Co. strongly recommends that your sprinkler system is repaired so that it will become compliant. The fire sprinkler system as-is may not work properly due to the referenced deficiencies/impairments and may not extinguish, suppress or control a fire. This is a safety hazard and may contribute to damage or injury to your property and individuals in t
6/6/23 Sent email regarding inspection DH Sprinkler Repair The 4" water flow switch on the east riser does not operate properly. The tech tried adjusting the switch and it still did not work properly. The tech will remove and replace the switch. NOTE: To replace the switch, the system will need to be drained and the water will flow to the parking lot. The customer will need to provide salt in case of water freezes. The tech will remove and replace (3) outdated water gauges.