Zack was very professional, he did a good job and in a timely fashion.
good hard workers
Sean was so quick to respond to our emergency repair today and appreciate him. Sean and Esmeralda worked so quickly together to get a proposal to me.
easy to work with
good job and fast
,Rich Johnson Manager, Alex is excellent prefer he does all of serve work always.
KITCHEN HOOD FIRE SUPPRESSION SYSTEM: Deficient aspects noted during testing - 1. We propose to Reconfigure/Twist around the Relief Valve to face towards front of system, so that inspector may safely complete water pressure test at semi-annual intervals. Not installed in an accessible manor. 2. Replace LT-20 Agent Discharge Cartridge with the proper LT-30 Cartridge due to size of the fire suppression system and manufacturers specifications. - repair -
5 2.5 BC IN OFFICE: FIRE EXTINGUISHERS: FROM RECENT INSPECTION, WE NOTED THE FOLLOWING SERVICE NEEDED FOR 2020 CODE COMPLIANCE - (1) 2.5#ABC OFFICE EXTINGUISHER REQUIRES 6-YEAR MAINTENANCE SERVICE - we propose to repair - Portable Extinguishers Repair
Annual Fire Extinguisher Inspection (7 FE's) Annual Exit & Emergency Lighting Inspection (9 units)
Annual Emergency/Exit Light Inspection (2 Units) Annual Fire Extinguisher Inspection (4 FE'S)
Annual Fire Alarm Inspection (18 Devices) (Edwards 5754-B2Z) Annual Sensitivity Testing
Suggested: 13 of the 15 stings on site are due for HT this year. Spoke w Criss from site. Return w 13 stings for swap.
Semi-annual Fire Alarm Inspection (86 Devices) (Simplex 4010) While onsite for Inspection look at trouble on panel horn strobes
Completed Annual Fire Extinguisher and Emergency Light inspections for 2020
Completed Annual Smoke Alarm Inspection for 2020
Completed Annual Nurse Call inspection for 2020