Zack was very professional, he did a good job and in a timely fashion.
good hard workers
Sean was so quick to respond to our emergency repair today and appreciate him. Sean and Esmeralda worked so quickly together to get a proposal to me.
easy to work with
good job and fast
,Rich Johnson Manager, Alex is excellent prefer he does all of serve work always.
Completed Annual Fire Alarm inspection for 2021
Completed annual Fire Alarm inspection for 2021
Per Rich - needs system tested to see if its functional - he will meet you onsite to walk through it all call 30 mins out 989-860-7789
Completed Annual Fire Alarm and Bi-Annual Smoke Detector Sensitivity inspections for 2020
FACP clear and Normal upon arrival. Tested AV’s . Upon Testing Only New Devices Failed to Function, After Further Trouble shooting Found Found that New Devices had not been wired and New Loop at NAC PNL had not been wired into NAC PNL. Wired AV in Business Center and Tested. Loop going in and out of business center was existing and AV Functioned when tested again. However the rest of the new devices are wired in and ready. ***Customer must get with installing Company to see if adding Additional AV Devices to Existing system loop is possible or if they have to add an additional booster power Supply. Currently as it stands now new Devices are wired and wire at NAC PNL is prepped for Additional NAC PNL being added. Will have to return when NAC PNL is added to tie in New loop and Test new devices.
KITCHEN HOOD FIRE SUPPRESSION SYSTEM: Deficient aspects noted during testing - 1. We propose to Reconfigure/Twist around the Relief Valve to face towards front of system, so that inspector may safely complete water pressure test at semi-annual intervals. Not installed in an accessible manor. 2. Replace LT-20 Agent Discharge Cartridge with the proper LT-30 Cartridge due to size of the fire suppression system and manufacturers specifications. - repair -
5 2.5 BC IN OFFICE: FIRE EXTINGUISHERS: FROM RECENT INSPECTION, WE NOTED THE FOLLOWING SERVICE NEEDED FOR 2020 CODE COMPLIANCE - (1) 2.5#ABC OFFICE EXTINGUISHER REQUIRES 6-YEAR MAINTENANCE SERVICE - we propose to repair - Portable Extinguishers Repair
Annual Fire Extinguisher Inspection (7 FE's) Annual Exit & Emergency Lighting Inspection (9 units)
Annual Emergency/Exit Light Inspection (2 Units) Annual Fire Extinguisher Inspection (4 FE'S)
Annual Fire Alarm Inspection (18 Devices) (Edwards 5754-B2Z) Annual Sensitivity Testing
Suggested: 13 of the 15 stings on site are due for HT this year. Spoke w Criss from site. Return w 13 stings for swap.
Semi-annual Fire Alarm Inspection (86 Devices) (Simplex 4010) While onsite for Inspection look at trouble on panel horn strobes
Completed Annual Fire Extinguisher and Emergency Light inspections for 2020