Logan was great came in and completed tasks without causing interruption to our operatoin.
Matt was very pleasant and told me exactly what he was at the school to do. I have no idea what the pricing was; my corporate office sets up the service.
4/2 Confirmed with Lexie. NO cooking at 10:00 AM km Kitchen Suppression Inspection Semi-Annual Kitchen Hood Fire Suppression System Inspection Deficiency: Number of Systems failed : 1 Deficiency: System does not have a discharge warning device.
Completed Annual Fire Extinguisher and Emergency light Inspections for 2021
Installed 2-New 5 lb ABC Extinguishers Mounted/Sealed and Tagged
Replaced 5-Battery Operated Smoke Alarms with Customer Supplied (AA) Batteries and Tested ***All Systems Normal and Reset ***
Kitchen Suppression and Portable Extinguishers Inspection
9/4 Approved by Linda, Needs this done before Thursday! DO NOT MISS! km Kitchen Suppression Inspection Pyro Chem PCL 300/300: Annual Inspection of Kitchen Fire Suppression system Annual Inspection of PCL-300/300 and PCL-300 Hood Suppression Systems [PCL-300/300 (2)links (10)nozzles , PCL-300 (3)links (5)nozzles]