Gerald was very thorough and very friendly throughout the process. Thank you!
Arrived On site FACP (Fire alarm control panel) Reflected NAC 2 Trouble Checked booster panel, found booster panel with out its AC Power Light On and Circuit board buzzing. Recycled AC and battery power. Panel still reflects same. Booster Panel is not recognizing its AC or Battery. However the NAC 2 Trouble appears to have gone away. Tested Fire Alarm system, system functions properly when Fire alarm is activated. Load tested (Customer Supplied Batteries) Batteries passed showing 12.6 volts and 11 amp hours each. Fire Panel is clear and normal at this time. However the Booster panel does require replacement. Informed staff that NAC 2 Trouble may come back over weekend until Booster Panel is replaced.
Annual Fire Extinguisher Inspection (6 FE) *Per Matt Briggs don't send site survey*
Alarm Systems Inspection
Portable Extinguishers Inspection
Portable Extinguishers and Emergency / Exit Lights Inspection
smoke detector located at the top of the basement stairs doesn't have a date code- - repair Furnish necessary parts and labor to supply new bracket and mount extinguisher in the white van
SD BEDROOM HALL RIGHT OF Living Room: BATTERY OPERATED ONLY SD IN HALL RIGHT OF LIVING ROOM IS PAST DATE COSE. DATE CODE IS 2001 - repair
AS IN BEDROOM # 1 RIGHT OF LIVING ROOM TRIPS PANEL BUT THE LED DOES NOT WORK AT ALL AND SHOULD BE REPLACED. I WAS LATER TOLD BY STAFF THAT A PIPE HAD BROKEN ABOVE THAT ROOM BACK IN JAN OR FEB 2019. - repair
Sensitivity Testing (4 smoke detectors) Annual Fire Alarm Inspection (20 devices) (Simplex 4004) Annual Fire Extinguisher Inspection (6 FE)