11/29/22 Emailed regarding inspection DH 11/14/22MV Called Costco and spoke MOD, Gm is calling back when they can get us in Sprinkler Inspection Semi-Annual Sprinkler Inspection (Annual done 2 times per yr) (4 Wet and 1 Dry Sprinkler Systems) Deficiency: There is no evidence of five-year internal obstruction investigation of dry sprinkler system. Deficiency: There is no evidence of five-year internal inspection of dry alarm valve. Deficiency: Sprinkler gauges are due for a change. Deficiency: There is no evidence of five-year internal inspection on dry sprinkler risers. Deficiency: Which sprinkler systems will need gauge chains a total of eight. Deficiency: There is no evidence of five-year internal inspection of fire department connection. Deficiency: There is no evidence of five year Hydro test on fire department connection. The On the outside is a STORTZ connection.
11/7/22 Sent off for cost for Tamper. DH Tech was onsite to service an issue with an active tamper supervisory. Tech noted that the switch would need to be replaced. Sprinkler Repair Deficiency: Tamper switch on main os&y is starting to go bad. When having my meter hooked up to the switch it half goes in to alarm. Suggest replacing the tamper switch with a new switch. Will need 1- potter os&y switch.
Emergency / Exit Lights Service Call