8/17 Scheduled with Neil mh Portable Extinguishers Inspection Annual Extinguisher Inspection
Alarm Systems Inspection Annual Duct Detector Inspection
Alarm Systems Repair
Replaced FACP Batteries that were Deficient from recent inspection also checked FACP phone line 1 Trouble. NTFD Customer of Telephone issue and to contact phone company.
Tested duct smoke and tested *** All Systems normal and reset ***