Great service and a professional installation.
Explained the problem and investigated it more than other company's.
You have a customer for life thank you
Timely and organized... very thorough and efficient
This was for inspection of fire suppression system and fire extinguishers. All were inspected and a search was made through both buildings to confirm that no fire extinguisher was missed. I appreciated that the inspector arrived earlier than scheduled time.
Completed annual Fire Extinguisher inspection for 2021
Corrected Deficiencies from recent inspection
Heat Detectors above Reception Desk and in Directors office are not tied into system and require removal or repair. Areas are currently covered by smoke detectors. - repair Heat Detectors throughout (4) require replacement due to age/condition. Detectors reflect Manf Dates from 1983 to 1999 4 - System Sensor 135 degree fixed / ROR detectors - repair Phone line 1 has voltage, no dial. Phone line 2 has heavy static on line. Phone lines are in disrepair and have been a continuing issue per the Director. Recommend installation of Cellular Communicator at location. - repair This quote is for the repairs and to add cellular communication to the fire alarm panel .
Completed Annual Fire Extinguisher inspection for 2021