The rep that services our system is always so nice and professional.
They have used Fire Pros for a while now at my place of work. They are very reliable and pleasant to work with. Dan was very thorough and expedient when he recently visited to inspect our fire extinguishers.
Completed annual Fire Extinguisher inspection for 2020
Completed annual Smoke/Co Alarm inspection for 2020
Retested Horn/Strobes after FACP Replacement found additional issues and wrote up Deficiencies for new service provider.
Replaced NAC PNL B2-5 In Hallway by A216 Above Drop Ceiling (Existing Old Notifier FCPS-24 was in trouble on FACP / after further Trouble Shooting found That Out-put 1 was Fried and was not recognizing loop or end of line resistance) Tested Horn/Strobes and Reset. system. ***Trouble Cleared off FACP*** Upon Arrival FACP also stated Supervisory LCD 80 (This Trouble is due to the remote Annunciators being removed due to construction) Work Approved by Scott Ballard
Replaced RTU-2 Supply (On-Roof) Duct Smoke Detector that was water damaged Wired, Tested and Reset. ***All Systems Normal and Reset***
Arrived on site FACP Showing ***All Systems Normal***Checked FACP History (Panel Shows Pre-Action System Trbl) Went To Boiler Room and checked Pre-Action System History. (History Showed System Low Battery/No Battery) Batteries we’re Bulging and Required Replacement. ***Replaced 2-12 volt 7 ah Batteries and Reset Date and Time ***All Systems Normal and Reset ***
Replaced 2-12 volt 18 ah batteries that failed load test ***All Systems Normal and Reset ***