Everyone is friendly and easy to work with. They are great with fully explaining the scope of work and the reasoning behind the services they perform.
Response from Fire Pros Inc:
Thank you for leaving a review, we greatly appreciate your feedback! Ryan is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Work was done and explained professionally; nice personality and proficient.
Always easy dealing with the Fire Pros crew
The techs are always nice and professional
The gentlemen that conducted the inspection and service were professional and personable. They also had suggestions that were helpful to overall safety for the plant. Thank you!
Hard scheduled w/ Shop manager Al Portable Extinguishers and Fire Door Inspection Annual Fire Extinguisher Inspection (5 FE) Fire Doors (2 Fire Doors)
Annual kitchen suppression system inspection Range Guard 6 gallon (only once per year per Curtis) add a nozzle to protect the steamer. Tee off of the nozzle directly next to the steamer. Justin has pics if needed.
Josh called System Trip over machine on special hazard - emptied 6 of the bottles
Annual Fire Extinguisher Inspection
Return to install 2 new smoke heads.
The smoke detector bases in the 2nd floor server room for the Fike SHP PRO panel are bad. Need to replace with 2 Hochicki photo electric smokes and bases. I temporarily bypassed the resistor bases to give the customer a working system, but the smoke loop wiring is unsupervised as is. - repair
Josh called needs service on alarm - trouble
Semi-annual ECARO 25 suppression system inspection.
Semi annual kitchen suppression inspection
Annual Fire Extinguisher Inspection (15 FE)