The tech was very knowledgeable and helpful. Thanks!
Brandon came into today do inspect our equipment today and was great and very friendly.
Sean did a great job.
Everyone is friendly and easy to work with. They are great with fully explaining the scope of work and the reasoning behind the services they perform.
Response from Fire Pros, LLC:
Thank you for leaving a review, we greatly appreciate your feedback! Ryan is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
FIRE EXTINGUISHERS: From our recent inspections, we noted the following service needed for code compliance - FOR PROPER PROTECTION / COVERAGE, THE FOLLOWING IS NEEDED: (1) 10#ABC fire extinguisher installed in SW Storage room (1) 10#ABC fire extinguisher installed in machine room in middle of shop (2) 9.5# clean agent fire extinguishers installed - one to quality room and one in EDM room (1) 5#ABC fire extinguisher installed in upstairs office area - we propose to repair - Portable Extinguishers Repair
Annual Fire Extinguisher Inspection (4 FE) Annual Exit & Emergency Lighting Inspection (10 units) Portable Extinguishers and Emergency / Exit Lights Inspection
Fire Alarm Inspection (Common Areas Only)
Dry Back room of Gas Station On riser: Perform a full flood trip test on the dry system. The purpose of completing a trip test for a dry pipe valve, be it a partial test or a full test, it to ensure that the system will operate. The full trip test of a dry pipe system allows for a comparative assessment of the water delivery time that can reveal significant delays in the system operation. NFPA 25 (220.127.116.11.2) Dry pipe valves should be trip tested in the spring to allow time before the onset of cold weather for all water that entered the system or condensation to drain to low points or back to the valve. NFPA 25 (18.104.22.168.2.2) Every three years and whenever the system is altered, the dry pipe valve shall be trip tested with the control valve fully open and the quick-opening device, if provided, in service.
Annual Fire Extinguisher Inspections (approx. 20 FE's total - 2 buildings on site) Portable Extinguishers Inspection