The tech was very knowledgeable and helpful. Thanks!
Brandon came into today do inspect our equipment today and was great and very friendly.
Sean did a great job.
Everyone is friendly and easy to work with. They are great with fully explaining the scope of work and the reasoning behind the services they perform.
Response from Fire Pros & Fire Systems of Michigan:
Thank you for leaving a review, we greatly appreciate your feedback! Ryan is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Work was done and explained professionally; nice personality and proficient.
Always easy dealing with the Fire Pros crew
The techs are always nice and professional
Portable Extinguishers Inspection
Annual Fire Extinguisher Inspection (5 FE) Fire Doors (2 Fire Doors) Portable Extinguishers and Fire Door Inspection
Completed fire extinguisher inspection and emergency light inspection.
Per call from Nathan, the alarm has gone off multiple time since we performed service. Need to check the delays on all switches to assure they are set correctly or if they need replacement. Remove and replace the 4" flow switch because the current one is not operational. Need to return and replace switch that is bad false alarm happened around 12:30 pm
Per call from Nathan, the alarm has gone off multiple time since we performed service. Need to check the delays on all switches to assure they are set correctly or if they need replacement.
Semi-Annual Kitchen Suppression System (PCL-350; 3.5gal)
Mechanical room by room 101: Remove and replace the outdated water gauge. NFPA 25 (18.104.22.168) Gauges shall be replaced every 5 years Mechanical room by room 101: Remove and replace the painted covers on concealed sprinkler heads located in the girl's restroom, hall by room 129, classroom 117, and the men's restroom. NFPA 25 (22.214.171.124.1) Any sprinkler that shows signs of any of the following shall be replaced; (6.) Paint other than that applied by the sprinkler manufacturer Pull (2) quick response concealed sprinkler heads and (2) quick response pendents dated 1995 & 2000 to send to UL For testing. These have been in service for more than 20 years and due for testing. New sprinkler heads will be installed in place of the ones pulled. NFPA 25 (126.96.36.199.1.3) Sprinklers manufactured using fast-response elements that have been in service for 20 years shall be replaced, or representative samples shall be tested and then retested at 10-year intervals.