Matt did a great job! It is yet to be determined on whether the splitting of the inspections needed will be acceptable due to perceived cost implications.
Tyler did his job in a professional & courteous manner. I was happy to have the opportunity to work with him.
Brandon is knowledgeable of his work and professional with delivering a great customer experience.
Arrived during given time slot, was respectful of our office and staff.
Can't rate cost do not know pricing.
Brandon was clear and concise in his duties. He went right to work after a briefing and completed the job efficiently. I did find that after researching replacement cost of one of the exit/emergency lights, the unit could have been replaced, with new, at half the price, although, whether the quality is the same or not, i don't know.
Portable Extinguishers Inspection
Portable Extinguishers Service Call
Annual 90 minute load test inspection on em/exit lights (20 units) Semi-annual Kitchen Suppression System Inspection PCL 2.4 gal
Emergency / Exit Lights Repair
Annual fire extinguisher and emergency/exit light inspection
H EAST HALLWAY TROUBLE HORN: TROUBLE HORN DID NOT FUNCTION IN EAST HALLWAY. NEED TO QUOTE TO REPLACE OR TROUBLE SHOOT. - repair
Return (3) FE pulled during inspection on 12-10
Annual Fire Extinguisher Inspection (12 FE)
Fire alarm inspection.