We have used alex with fir pros many times for commercial jobs and they always do amazing work. Due to conditions beyond their control, they were not able to help us on the most recent job we had requested, but Alex explained very well what has to happen and how we should go about correcting some things. 5 stars for sure, and we always recommend them.
Jared was great. Called as I requested. He explained everything as he went to each floor. He also went over the whole inspection when he was finished. Made sure the contact information was correct. A great job out of the way.
Awesome crew, did the job well and in a timely matter.
Response from Fire Pros, LLC:
Thank you for leaving your review! We greatly appreciate your feedback and are glad that we provided you valuable service! At your convenience, please consider sharing your experience on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
9/3 Service requested by Sonja. New hours now, so they are not cooking at 11:00 AM. Sonja will be on site for you km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Semiannual Kitchen Inspection Ansul R102-D6 (4)500 links (2)360 links (11)Nozzles Deficiency for R-102 6G: Exhaust fan above convection oven not working prior to test. Deficiency: 1- K-Class fire extinguisher out of hydro date.
8/20 Confirmed with manager Yasmine, she'll let manager Shareeka know of the appt. km Kitchen Suppression Inspection Semiannual Kitchen System Inspection
Annual Extinguisher Inspection Portable Extinguishers Inspection 8/20 Scheduled with Mario mh
8/20 Arrive at 10:30 to swap out loaner tank with new tank. Nick wants you to check all the extinguishers that are in the VIP room (it looks like Lenn did extinguishers when he was there on 8/17) km 8/8/11 Approved by Joe Kakos. Do this at the same time as semiannual service and annual exts. km Perform required 12 year hydrostatic test on the kitchen fire suppression system agent tank and replace agent with new. All work done in accordance with NFPA 17A. Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC.
8/4 Approved by Marc Wolney. No cooking right now. km Kitchen Suppression Inspection Semi-annual Kitchen System Inspection Range Guard RG-1.25 (2)360 links (4)Nozzles
8/3 - scheduled with Marcel, mgr. Told him between 1-3 p.m. mh Portable Extinguishers and Emergency / Exit Lights Inspection Annual Extinguisher Inspection ( 12 ABCs ) Annual Emergency/Exit Light Inspection Inoperable Deficiency: Exit light combo units located abov front entrance and the back of service area need replacing.
7/29 Approved by Yolanda, her sister Patty will be in the kitchen for this service. km 6/24 Yolanda will call back km 4/14 12:30 LM on VM and emailed Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semi-annual Kitchen System Inspection Deficiency: PCL-300 tank out of hydro date.
7/30 LM for Mo reminding him of our appt., called location and talked to Malok, she sent him a text reminding him km 7/29 Appt approved by Mohammad. He'll be there at 7:30 for us. Understands no cooking, can't be hot. km 4/16-Mohammad will call back to schedule/corona hold NW TD 2.28.20 VM Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Semiannual Kitchen Inspection Ansul R102-D6 (2)500 links (2)360 links (9)Nozzles Deficiency for R102-D6 6G left of hood: Electric connections made inside of the automan. Inoperable Deficiency: 1- 5# abc fire extinguisher needs to be recharged. 1- K-Class fire extinguisher due for hydro test.
7/20 Scheduled with Greg. MH Portable Extinguishers Service Call Recharge of extinguisher on forklift