I am very pleased with your staff and service
Alex is attentive to detail and advises me of any issues that he incurs.
would highly recommend
Jim was extremely friendly, efficient, quick and thorough with his semi-annual inspection of our taproom. Did an excellent job and kept the loud alarm check portion to a minimum!
The tech knows his job was very polite and professional. It would be so nice if all contractors were like him. He is an asset to your company. Thank you
After the technician showed up, completed the inspection of the galley fire suppression system and extinguishers but didn't show up with extra fire extinguishers to complete the hydrostatic inspection of the fire extinguishers that needed to be tested. waiting to hear back from company to find out when the technician will show up and complete the rest of the inspection.
I’ve had the pleasure to walk with Bob Greenwood, and I must say he was very efficient but beyond that he has an amazing approach and know how to treat a client. We would be more than happy to have him work at our jobsite any day!
My opinion of your company and the reps who make visits to our building is to be commended for time and talent. Thank you
10/15 Confirmed with Priscilla. Emailed confirmation to Team. km Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection Semi annual inspection of the kitchen system Annual fire extinguisher inspections Annual e/light inspections Deficiency: Kitchen suppression Ah
10/19 Gas on, appt confirmed with Jen. km 10/15 No gas to building. Appt. canceled tentatively km 10/8 Jenn, owners rep. called for service. Cell: (734) 346-1767 Emailed confirmation and scope of work km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Semi-Annual Kitchen Suppression System Inspection
Annual inspection of fire extinguisher (Includes entire bldg. Starfish, Holy Cross, and Matrix)
10/6 Rescheduled with Brenda Jackson...TUESDAY ONLY! They are only in the office on Tuesdays km 9/29 - Brenda called to schedule mh 9/24 LM with Shawn's office for them to call us. km 9/23 - called and left message mh Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is may not work properly due to the deficiencies described below and may not properly extinguish, suppre
Semi-annual Fire Extinguisher Inspection (3 FE) Elight inspection