Alex was excellent, he was thorough and a breath of fresh air. I loved his demeanor and professionalism.
i would highly recommend you guys.thank you.
George was very professional and thorough in his job. Explained every detail of what he went over and made sure any questions were answered
Alex is informative, thoughtful and has expertise regarding his job.
very professional - mission accomplished!
Came exactly when scheduled, finished early!
Corrected Deficiency from recent inspection And Updated 2020 Report ***All Systems Normal and Reset ***
1/14/21 Confirmed with Emma for Monday 1/18/21. sm 1/11/21 Called and left Message to Schedule SM Emergency / Exit Lights and Portable Extinguishers Inspection Annual inspection of e/lights (3) Annual inspection of fire extinguishers
1/8 Confirmed with Chad. km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Semi-Annual Kitchen Suppression System Inspection PyroChem PCL-460 (3)500 links (1)360 link (7)Nozzles Deficiency: Number of Systems failed : 1 Deficiency: System not connected to a building fire alarm or discharge warning device.
Notice of Non Compliance and Repair Proposal Fire Systems of Michigan recently inspected the fire extinguishers at your establishment in accordance with applicable state statutes, local fire codes and NFPA guidelines. While inspecting your extinguishers, they were determined to be "Non-Compliant" per local fire codes. The attached proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Please contact me as soon as possible to review the attached proposal and schedule the repair to your fire extinguishers. I look forward to working with you to bring your extinguishers into compliance. To discuss this proposal, please contact: Randy Pattee. Phone: 248-397-6563 Email: firstname.lastname@example.org EQUIPMENT REPAIR AGREEMENT This Agreement between FIRE SYSTEMS OF MICHIGAN (Company) and you (the Customer) provides for repair services only on the equipment indicated on the "Scope of Work" and "Services to Be Comp
1/8 Confirmed with Paul He'll be on site for you. km 12/21 LM for Paul km 10/13 Pastor will call back. k m Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection ( 1 FEs ) Semiannual Kitchen Suppression System Inspection ( 1 Pyrochem 3G )
12/21 Confirmed with Kevin, they won't be open yet, so no cooking. km Kitchen Suppression Inspection Semi-annual Kitchen System Inspection Ansul R102-S3 (2)500 links (2)360 links (6)Nozzles Deficiency for Ansul R-102 3 Gallon Right Side of Hood: There is no divider between fryer and range.