TD 2.28.20 VM for Walt - Walt called back confirming 1p Kitchen Suppression Inspection Semiannual Kitchen System Inspection PyroChem PCL-460 (1)500 link (3)360 links (10)Nozzles Deficiency: Need to add detection over fryer Deficiency for Pyro Chem PCL 460 right of hood: Appliance line piping is galvanized. Galvanized pipe cannot be used with wet chemical suppression system. Deficiency for Pyro Chem PCL 460 right of hood: System tank is over flow points. Tank has a max of 15 flow points system is currently at 17 flow points.
Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection (13)ABC (2)K Semiannual Kitchen System Inspection Ansul R102-S3 (3)360 links (6)Nozzles Ansul R102-S3 (2)360 links (3)Nozzles Deficiency for R-102 3G right of hood: Deep fryer under main hood is undetected. TD 3.2.20 Fabian confirmed reschedule 2/24-Fabian confirmed the semi-annual kitchen suppression inspection/aware of alarms NW
Replaced 3 Heat Detectors that were Deficient from Recent Inspection (kitchen,Laundry Room,Basement HD’s) Tested And Reset System ***All Systems Normal and Reset ***
Replaced FACP battery that was Deficient from recent inspection ***All Systems Normal and Reset ***
Completed Annual Fire Alarm Inspection for 2019
Replaced Popeyes rear door pull station ***All systems normal and reset ***
Trouble shooted system Part required, will return